- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 15 Jun 2017
Torre Windsor office building fire
The 30 storey Torre Windsor office building was constructed in the 1970s. It consisted of a reinforced concrete core and six reinforced concrete columns within the floor plate area, and steel load-bearing mullions (steel edge columns) around the perimeter.
At the time of the design the relevant codes did not require these mullions to have any fire protection. The floor was of concrete waffle slab construction. There were ‘strong’ transfer floors at the 3rd and 17th levels.
A refurbishment programme was commenced in 2005, instigated partly to bring the building up to current fire standards through the installation of active fire prevention and resistance measures. These included protection to the external mullions, new fire doors, and the provision of a sprinkler system. A new external steel escape staircase was also included. At the time of the incident the fire protection to the mullions had been applied below the 17th strong floor (apart from floor 9) but not to those mullions above the 17th floor; the new sprinkler system was not operational.
During this refurbishment work a fire broke out on the 21st floor. The fire spread downwards to the 2nd floor, and upwards to the top of the building. It burnt for some 19 hours and engulfed the entire building. Although local progressive collapses occurred a total collapse was narrowly averted. The new staircase performed well. However, the building was later completely demolished.
The studies concluded that the fire spread as a consequence of the lack of operational fire doors, fire stopping and through radiant heat. Cladding failure worsened the situation by allowing the fire to spread between floors Several floors burnt simultaneously giving rise to very high temperatures as the size of conflagration resulted in a lack of cooling from external air sources.
 Consequential damage
In the absence of any protection the mullions weakened in the heat. A sufficient number lost their required load capacity causing sections of the building above the upper strong floor at level 17 to collapse. It is likely that only the presence of this floor prevented total progressive collapse. At lower levels none of the fire protected mullions failed.
 Conclusions from the investigation
An extensive investigation was carried out by INEMAC. Their key conclusions included:
The need to recognise that concrete structures continue to heat up during extinction of the fire and after the gas reaches its maximum temperature, even though the temperature on the surface of members begins to reduce. The need to acquire a better understanding of the effects of the cooling phase on concrete structures.
The need for a suitable and sufficient risk assessment from all foreseeable hazards during a refurbishment project. This is particularly important where the building may be occupied, and for intermediate stages which can pose unacceptably high risks unless managed properly (examples of fires occurring in the UK during construction/refurbishment would include the Broadgate office fire (1990), the Uppark House National Trust Property fire (1989) and the Beaufort Park development in Colindale (2006)).
Although the contractor is responsible for adequate on-site fire precautions during construction/refurbishment, on complex projects the designer has a key role to play at the design stage in the consideration of, for example, buildability issues, necessary contractual constraints, formalised methods of working.
This event demonstrates the benefits of ‘strongfloors’ and of alternative load paths, i.e. robustness.
This topic paper was originally published by SCOSS here.
 Related articles on Designing Buildings Wiki
Featured articles and news
This article examines the changing policy commitments and evolving definitions of the zero carbon home.
Researchers believe they may have created a 'game-changing' new form of concrete using graphene.
Grouting refers to the injection of materials into a soil or rock formation to change its physical characteristics.
Part of Designing Buildings Wiki, BREEAM Wiki will advance knowledge sharing for the BRE family of sustainability tools.
From the decorative to the utilitarian, and from the photographed to the forgotten.
New BRE book considers the progression from project-based knowledge creation to whole-life urban knowledge management.
This CIOB article explores the concept of value in building design and construction.
BREEAM and Measurabl announce integration to improve the financial performance of commercial real estate.
Rogers Stirk Harbour + Partners' release new images of soon-to-open 3WTC tower in New York.
A document can be called a bond or a guarantee. Does the name matter and what is the difference between them?
New briefing note is launched focusing on increasing knowledge of housing that promotes health and wellbeing.
Arbitration is a private, contractual form of dispute resolution used in the construction industry.