- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 12 Jan 2016
Mechanical ventilation with heat recovery MVHR
See also: Exhaust air heat pump.
- Helping to moderate internal temperatures.
- Replenishing oxygen.
- Reducing the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Creating air movement which improves the comfort of occupants.
- Mechanical (or ‘forced’) ventilation tends to be driven by fans.
- Natural ventilation is driven by ‘natural’ pressure differences from one part of the building to another.
Traditionally, many buildings were ventilated largely by natural ventilation or 'infiltration', with fresh air entering spaces when doors or windows were opened, or through gaps in the fabric of the building. However, as the building regulations have become increasingly strict, and build quality has improved, buildings have become more air-tight and ventilation is increasingly provided mechanically.
Approved Document F, of the building regulations ‘Means of ventilation’ describes mechanical ventilation with heat recovery as, ‘continuous mechanical supply and extract with heat recovery’. It is commonly used in housing to extract stale air and supply fresh air whilst recovering up to 95% of heat that would otherwise have been lost from the extract air and using it to pre-heat the supply air.
Whole-house, or multi-room MVHR involves installing ductwork to each room, typically in ceiling voids, and running these ducts to a heat recovery unit, often located in the loft space. Air is continually extracted from rooms that might be warm and humid, such as bathrooms and kitchens. This is passed through a heat exchanger in the heat recovery unit where ‘waste’ heat is recovered from the air before it is rejected to the outside. The heat exchanger uses the recovered heat to ‘temper’ incoming fresh air that is used to supply the non-humid ‘habitable’ rooms such as bedrooms and living rooms. Tempering the incoming air reduces the need for heating, and so reduces energy use.
The standard, background level of ventilation can be boosted manually or automatically when bathrooms or kitchens are in use. The heat exchanger can be by-passed in warmer conditions so that the fresh supply air remains cool. Typically filters will be included in the system to remove potential pollutants such as pollen and dust form the supply air.
Care must be taken when installing MHVR to ensure that ducts do not provide a flanking route for noise to transmit between spaces. It is also important to properly size and locate the heat recovery unit and ductwork so that any sound generated by the system itself is minimal.
Regular maintenance is required to ensure that fans are operating correctly and filters remain clean.
MVHR ductwork should be arranged so the connection to the world is as short as possible. Insulate both ducts that connect the MVHR to the world. This is intended to prevent condensation on the outside of the incoming pipe and the inside of the outgoing pipe. Have all the duct runs between rooms and MVHR within the thermal envelope of the house. This means they need no insulating. The air that they're carrying is as warm as the house air, essentially so if they run through a cold space they will cool. This is either your warmed fresh air that is cooling, or it's your heat laden stale air. Loss of heat from either represents a loss of heat from the warm envelope.
So between room and MVHR you care about losing the valuable heat. Between the MVHR and world you care about the nuisance condensation. Being insulated or in a warm envelope addresses both problems.
 Find out more
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air infiltration testing.
- Building services.
- Cross ventilation.
- Displacement ventilation.
- Domestic ventilation systems performance.
- Exhaust air heat pump.
- Flanking sound.
- Heat recovery.
- Interstitial condensation.
- Mechanical ventilation.
- Natural ventilation.
- Stack effect.
- Thermal comfort.
Featured articles and news
Rebuilding could take 20 to 40 years.
RSHP’s high-rise residential towers win a tall buildings award for excellence.
BSRIA study reveals strong growth in 2018.
Dame Judith Hackitt confirmed as keynote speaker – one year on from the Hackitt Report.
Save £100 on tickets.
Modern slavery in the construction sector.
What to bear in mind when claiming damages in construction.
How do we achieve sustainable clean-water infrastructure for all?
What you should know when appointing an architect.
A brief history plus some new developments.
How computational fluid dynamics (CFD) helps building design.
The Hong Kong Harbour Area Treatment Scheme (HATS).
'Expressions of interest' for construction contracts.