- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 05 Jul 2021
Displacement ventilation (DV) first emerged as a ventilation strategy in the 1970’s. It can lower energy consumption and improve air quality by supplying ‘fresh’ air direct to the occupied zones in buildings.
In ‘conventional’ mixing ventilation systems, air is supplied to occupied spaces at a relatively high velocity at ceiling level. This supply air mixes within the internal air, and a proportion of the mixed air is then extracted. Mixing ventilation systems may also re-circulate some of the internal air with the supply air.
Displacement ventilation systems supply low-velocity ventilation air at low level, close to the floor, creating a pool of cool, fresh air in the zone where people are likely to be. This air then heats up when it comes into contact with building occupants, equipment, lighting and so on. As it becomes warmer, so it becomes more buoyant and rises through the space, creating a thermal plume that drives ‘stale’ air upwards, where it is extracted. So, the fresh supply air ‘displaces’ the stale internal air.
Displacement ventilation tends to operate with lower air velocity, lower fan speeds, and higher supply air temperature compared to mixing ventilation systems. This avoids draughts and large temperature differences within the occupied zone which might otherwise cause discomfort.
Air is supplied through special, low-velocity diffusers which must be relatively large in area to provide adequate ventilation at low speeds. Diffusers are typically wall mounted, corner mounted or freestanding. The lower fan speed associated with displacement ventilation tends to result in less noise.
Displacement ventilation can supply cool air, or can simply supply fresh ventilation air, sometimes with cooling provided by other sources, such as radiant chilled ceilings. It can be used to provide low level heating, but is not a particularly effective method of heating, as warm air will tend to rise rapidly, before it has properly heated the occupied space.
In small spaces, such as school classrooms, displacement ventilation may be relatively straightforward and might be designed by following accepted ‘rules of thumb’. However in more complex spaces such as theatres, computational fluid dynamics (CFD) analysis might be necessary to model air flows and help size equipment.
NB Underfloor air distribution (UFAD) is sometimes considered to be a form of displacement ventilation. This uses the underfloor plenum beneath a raised floor to provide air through floor diffusers directly to the occupied zone. However, in some UFAD systems, the available diffuser area for UFAD is smaller, and so the supply velocity higher and supplied through diffusers that create greater mixing of the internal air than is generally found in displacement ventilation.
 Related articles on Designing Buildings Wiki
Featured articles and news
Temperature in buildings, explained on DB
Main barrier to entering the profession, new study reveals.
On Levelling-Up and Regeneration Bill.
Over 70 managers and organisations shortlisted for the 14 awards.
From biometric to electrical current, chemical and more.
Changes are due to come into force on 1st October 2022.
Heed advice and insight of this report IPA tells the government.
From the Commonwealth Association of Architects.
For the Levelling Up, Housing & Communities Committee.
BSRIA's Technical Director reflects on recent weather patterns.
A national valuation to fund old-age pensions.
The world’s largest Commonwealth memorial to the missing.
Long after the end of the defects liability period.
Occupant satisfaction and wellbeing in buildings.
From the simple to the complex.
And the UK Government guidelines.
Commitment agreed to by major built environment bodies.
Electrical skills, low carbon, high-tech and the building services revolution.
Ultra-deep drilling with millimeter-wave beam technology.
Looking at the built environment from space.
BSI standards 8671, 8672 and 8673.
Bringing life to burial grounds.
From failed modernism to twenty-minute neighbourhoods.
The gates process and change control.