Lighting of construction sites
In order that construction work can continue effectively and safely in periods of insufficient natural light, it is important that a site is fitting with suitable artificial lighting. Lighting can be used internally for general movement and working on the site itself, externally for illuminating entry, storage and circulation areas, and can also be an effective form of deterrent for trespassers.
There are a wide range of lamps available, from simple tungsten filament lamps to tungsten halogen and discharge lamps. Site lighting is generally run off mains electricity at a voltage of 230 V, rather than through the use of generators. Sometimes it can be necessary to reduce the voltage to 110 V.
For an appropriate lighting plan to be drawn up, the types of activity that will be likely to require lighting need to be specified. These activities can then be given an illumination target (with the unit being lux). Lamps are often given a measurement in lumens (lm), which is the total quantity of visible light emitted. One lux is one lumen per square metre.
Examples of recommended minimum target values for building activities include:
- Circulation: 10 lx
- Materials handling: 10 lx
- Circulation: 5 lx
- Working areas: 15 lx
- Concreting: 50 lx
- Carpentry and joinery: 100 lx
- Bricklaying and plastering: 100 lx
- Painting and decorating: 200 lx
- Site offices: 200 lx
- Drawing board positions: 300 lx
While manufacturers will often specify the best arrangement for lamps according to required use, it is common practice to plan for at least twice the recommended target values. This is because lamps in use can be subject to deterioration, dirt or other conditions that reduce their performance.
It is possible to calculate the required lumens for a particular need with the following equation:
Total lumens required = area to be illuminated (m2) x target value (lx) / Utilisation factor
Where the utilisation factor is 0.23.
Once the lamp type has been chosen, the required number can be calculated with the following equation:
 Site arrangement
Lighting can be arranged on site in a static formation, where lamps are fixed to support poles, masts or items of plant such as scaffolding and tower cranes, or, it can be arranged locally, as and where work is progressing, by the use of moveable supports or being hand-held with trailing leads.
To illuminate general working areas, festoon (overhead) lighting can be suspended from grids at regular spacings. These are usually tungsten filament bulbs, and both cable and lampholders must be appropriately weather-resistant.
The arrangement must be such that visual intrusion and light spillage are kept to a minimum, particularly in close proximity to residential properties and busy roads where it may cause nuisance or distraction. Where necessary, lighting should be provided to site boundaries to ensure the safety of passing pedestrians.
For more information, see How to work safely on a construction site in the dark.
 Related articles on Designing Buildings Wiki
- Construction phase plan.
- Daylight factor.
- Daylight lighting systems.
- Ergonomics in construction.
- General lighting v task lighting.
- How to work safely on a construction site in the dark.
- Improving visibility and resilience of buried services.
- Health and safety.
- Light obstruction notice.
- Light pollution.
- Pre-construction information.
- Rights to light.
- Site appraisal.
- Site information.
- Site layout plan for construction
- Site plan.
- Site facilities.
- Site office.
- Site storage.
- Site survey.
- Temporary site services.
- Welfare facilities.
 External references
- ‘Building Construction Handbook’ (6th ed.), CHUDLEY, R., GREENO, R., Butterworth-Heinemann (2007)
Featured articles and news
What will the General Data Protection Regulations (GDPR) mean for you when they come into force in May?
Business Secretary chairs a new taskforce to monitor and advise on mitigating the impacts of Carillion’s liquidation.
Sir John Armitt is appointed the new chair of the National Infrastructure Commission.
High quality and high density homes - is it what we need or is it storing up trouble?
Government announces its intention to strengthen planning rules to protect music venues and neighbours.
National Audit Office reports that there is little evidence that PFI offers better value than other forms of contracting.
What is liquidation and how does it apply to contractors in the construction industry?
Scrutiny is placed on Carillion's controversial 2013 decision to extend subcontractor payment terms to 120 days.
RSHP unveil their involvement in a boundary crossing which will provide a new entry point into Hong Kong.
With PFI currently under the spotlight due to Carillion, this introductory article explains what they are.
Estimates suggest that up to 30,000 small firms could be at risk of non-payment as a result of Carillion's collapse.