- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 16 Sep 2020
Lighting of construction sites
In order that construction work can continue effectively and safely in periods of insufficient natural light, it is important that a site is fitted with suitable artificial lighting. Lighting can be used internally for general movement and working on the site itself, externally for illuminating entry, storage and circulation areas, and can also be an effective form of deterrent for trespassers.
There are a wide range of lamps available, from simple tungsten filament lamps to tungsten halogen and discharge lamps. Site lighting is generally run off mains electricity at a voltage of 230 V, rather than through the use of generators. Sometimes it can be necessary to reduce the voltage to 110 V.
For an appropriate lighting plan to be drawn up, the types of activity that will be likely to require lighting need to be specified. These activities can then be given an illumination target (with the unit being lux). Lamps are often given a measurement in lumens (lm), which is the total quantity of visible light emitted. One lux is one lumen per square metre.
- Circulation: 10 lx
- Materials handling: 10 lx
- Circulation: 5 lx
- Working areas: 15 lx
- Concreting: 50 lx
- Carpentry and joinery: 100 lx
- Bricklaying and plastering: 100 lx
- Painting and decorating: 200 lx
- Site offices: 200 lx
- Drawing board positions: 300 lx
While manufacturers will often specify the best arrangement for lamps according to required use, it is common practice to plan for at least twice the recommended target values. This is because lamps in use can be subject to deterioration, dirt or other conditions that reduce their performance.
It is possible to calculate the required lumens for a particular need with the following equation:
Where the utilisation factor is 0.23.
Once the lamp type has been chosen, the required number can be calculated with the following equation:
Lighting can be arranged on site in a static formation, where lamps are fixed to support poles, masts or items of plant such as scaffolding and tower cranes, or, it can be arranged locally, as and where work is progressing, by the use of moveable supports or being hand-held with trailing leads.
To illuminate general working areas, festoon (overhead) lighting can be suspended from grids at regular spacings. These are usually tungsten filament bulbs, and both cable and lampholders must be appropriately weather-resistant.
The arrangement must be such that visual intrusion and light spillage are kept to a minimum, particularly in close proximity to residential properties and busy roads where it may cause nuisance or distraction. Where necessary, lighting should be provided to site boundaries to ensure the safety of passing pedestrians.
For more information, see How to work safely on a construction site in the dark.
 Related articles on Designing Buildings Wiki
- BREEAM Reduction of night time light pollution.
- Colour Rendering Index CRI.
- Construction phase plan.
- Daylight factor.
- Daylight lighting systems.
- Ergonomics in construction.
- General lighting v task lighting.
- How to work safely on a construction site in the dark.
- Improving visibility and resilience of buried services.
- Health and safety.
- Light obstruction notice.
- Light pollution.
- Pre-construction information.
- Rights to light.
- Site appraisal.
- Site information.
- Site layout plan for construction
- Site plan.
- Site facilities.
- Site office.
- Site safety.
- Site storage.
- Site survey.
- Temporary site services.
- Welfare facilities.
 External references
- ‘Building Construction Handbook’ (6th ed.), CHUDLEY, R., GREENO, R., Butterworth-Heinemann (2007)
Featured articles and news
Recognising past and present role models for the future.
So why not write something?
LETI publishes guidance for energy efficient home retrofits.
Predictions about adequate post-pandemic IAQ in non-domestic buildings.
Government publishes plans to 'build back greener'.
The contentious nature of claims associated with cladding, fire safety and EWS1 forms.
ECA comments on low-carbon heating systems initiative and Heat and Buildings Strategy.
Cinders and other forms of domestic rubbish created filth but also generated great wealth.
CIC 2050 Group requests input to find out priorities for future industry leaders.