- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Jan 2020
Improving fire safety design with coupled hybrid modelling
A new computer model can provide added insights into fire risks in complex buildings, and help engineers to develop robust fire safety designs. This coupled hybrid modelling has been investigated by Benjamin Ralph as part of a BRE Trust supported PhD studentship at the University of Edinburgh.
Fire engineers commonly use computational fluid dynamics (CFD)-based fire modelling to develop and test the designs of complex buildings. However, as these models are very complicated and this type of simulation takes an impractically long time to run, engineers typically reduce the size of the model to shorten the time needed.
The problem is that a simplified model may not be able to account for the entire building. That means that the ways in which fire and smoke might spread throughout the whole building cannot be fully determined, nor can the effect on the growth and spread of fire and smoke of parts of the building far from the fire. This can put limits on the ability of engineers to develop robust fire safety solutions.
One way of addressing this limitation is the use of ‘coupled hybrid modelling’. This combines the originally used model (which takes a long time to run) and another model (which takes a much shorter time) together. Fire engineers can thereby increase the model size to include more or all of a building, but still carry out a simulation in a reasonable length of time.
A literature review of existing coupled hybrid models identified a lack of collaborative working and the use of proprietary software. Therefore, a coupled hybrid model has been developed, based on the open-source and widely used fire model, Fire Dynamics Simulator (FDS).
A new computer model must be compared with real experiments to confirm that it can represent the real world within reasonable limits. Applicable experimental data were not found during an extensive literature search and discussions with applicable bodies. Therefore, to provide these data, a new experimental rig was specifically designed and built.
 Ventilation issue revealed
Data from the new rig were first used to examine potential holes in the current typical fire safety design model for complex buildings. This analysis showed that there are phenomena related to the two-way coupling of a fire and a shared ventilation system, which may not be captured by commonly used simple engineering methods – or addressed in current design guidance documents.
The new experimental data was then compared with the predictions of the coupled hybrid computer model, and the qualitative and quantitative differences highlighted. The computer model was found to predict fire hazards within the experimental set-up effectively, providing key information needed by future model users to ensure that their analysis is robust.
The original insights into how a total building system and a fire interacts, and the newly developed coupled hybrid model, can be used together by fire engineers. This will help them to deliver design solutions with more deeply understood fire life safety risks for complex buildings that incorporate mechanical ventilation systems.
 About this article
 Related articles on Designing Buildings Wiki
- Approved document B.
- Dry riser.
- Emergency services.
- Evacuating vulnerable and dependent people from buildings in an emergency FB 52.
- Fire damper.
- Fire detection and alarm system.
- Fire door.
- Fire protection engineering.
- Fire resistance.
- Fire safety design.
- Fire spread.
- Fire stopping.
- Flame technology.
- Ionisation smoke alarm.
- Joint fire code.
- Optical smoke alarm.
- Protected escape route.
- Protected lobby.
- Managing risks in existing buildings: An overview of UK risk-based legislation for commercial and industrial premises (FB 86).
- The causes of false fire alarms in buildings.
Featured articles and news
The admissibility of evidence.
How many can you name? 37 anyone?
CIOB respond to the points-based system.
When is the weather considered 'exceptionally adverse'?
ECA backs call for a rolling programme of rail electrification.
What does 'curtilage' mean and why does it matter?
Our duty to prevent harm and protect each other.
A quality perspective.
If buildings were people, they would be just starting to walk on two legs.
Air filtration and clean air standards.
The Dukes of Normandy and the second world war.