- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 26 May 2022
Closed system water treatment: BG 50 & VDI 2035
Following the 2021 release of the 2nd edition of Water Treatment for Closed Heating and Cooling Systems (BG 50/2021), BSRIA Engineering Investigations Lead, Chris Thompson, answers questions on what BG 50 is and how it relates to the VDI 2035 standard.
BG 50 applies to closed heating and cooling systems, providing guidance to achieve a well-maintained, functional closed water system. The guide includes a detailed outline of some of the methods and technologies used and provides an explanation of the science behind water quality and its importance in system maintenance. It is important to note that BG 50 is a guide and not a standard or regulation.
Should I use VDI 2035 or BG 50?
VDI 2035 and BG 50 should not be treated as comparable documents – they serve different purposes. Being aware of the differences between the documents is key to understanding and using each of them correctly.
VDI 2035 is a German standard, which has been widely used in Germany for many years and has grown in popularity in the UK, partly due to its non-chemical approach. There are currently two parts to VDI 2035, Part 1 and Part 3, with Part 2 having recently been withdrawn and its content included in the updated version of Part 1, which was published in March 2021.
VDI 2035 Part 1 Prevention of damage in water heating installations, Scale formation and water side corrosion is applicable for closed water heating systems and focuses on limiting damage caused by scale and water side corrosion in closed hot water heating systems with temperatures up to 100oC. Like BG 50, it contains a background of the scientific principles behind corrosion and scale formation, with particular attention drawn to the importance of oxygen in corrosion processes. This document places an emphasis on the fill water quality and reducing oxygen entry into the system, the main driver of corrosion processes. The chemical inhibitor addition method is referred to in VDI 2035 Part 1 as being a last resort to manage a system’s water quality where the electrical conductivity and pH of the fill water cannot achieve the levels recommended in the standard.
In the UK, the chemical inhibitor addition method is widely used to prevent corrosion issues, commonly alongside other methods. This has been proven to work but, as with other methods, if it is poorly managed or implemented, it can also lead to corrosion problems. The chemical inhibitor addition method does give resilience in terms of fill water and allows for unexpected entry of oxygen by passivating the metallic surfaces or binding with the free oxygen. Once adequately protected, the system should not require further chemical addition unless other factors deplete the chemical such as the presence of bacteria or the loss and replenishment of system water. As building services engineers will be aware, mistakes in management, often due to lack of knowledge or infrequent monitoring, can lead to the failure of this method.
One particular issue that is frequently reported to cause excessive air ingress leading to corrosion is incorrect pressurisation. To this end, BSRIA is working with industry to produce guidance on correct design, specification, installation, commissioning, operation, and maintenance of pressurisation in closed heating and cooling systems.
BG 50/2021 includes guidance on some of the technologies used to achieve compliance with VDI 2035 Part 1 but leaves details of achieving compliance to the standard itself. The role of BG 50 is to provide guidance on the science, technology, and management principles to allow the reader to make an informed decision or to help understand why a particular approach has been taken by the water treatment specialist. This may include chemical inhibitor addition, electrochemical water treatment, mechanical filtration, deaeration or a mixture of many methods, dependent on the system and its requirements. There is no one-size-fits-all approach for water treatment of closed heating and cooling systems.
To summarise, BG 50 is an overarching guidance document, outlining multiple methods of water treatment, the science and surrounding technologies involved in closed water systems. VDI 2035 Part 1 is a standard predominantly focussed on one method and the associated background science of treating and maintaining hot water heating systems.
Scientifically, the VDI 2035 approach is sound and through further adoption, education, and time, the application of this methodology across a range of materials and system configurations will be more widely and fully understood in the UK.
This article was originally published on the BSRIA website in April 2022.
- Biological fouling.
- BSRIA articles on Designing Buildings Wiki.
- BSRIA Water Treatment for Closed Heating and Cooling Systems BG 50/2021.
- Chilled water.
- Commissioning building systems.
- Heating ventilation and air conditioning.
- Training for pre-commissioning cleaning of pipework systems.
- Water treatment.
Featured articles and news
Two new research reports published by APM.
50% off APM Associate membership for Designing Buildings users.
A commentary from the insurance perspective.
In brief with further links.
A definitive book on a pioneer of green architecture.
Using heritage as a catalyst for reviving historic centres.
Declaration prioritising sustainable urbanisation adopted.
Some brief words about the actuator.
After 34 years at the Institute.
To support the next generation of engineers.
CIAT reporting from the Competition and Markets Authority.
Making sustainable construction number one priority.
Interview with ECA CEO.
Many provisions came into force on June 28, 2022.
With room to expand.
Refurbishment, Energy Efficiency, Indoor air and process.
Why building acoustic considerations must be non-negotiable.
Aluminium Composite Panels (ACP) is one example.
Inventors and innovators at ICE.
Life, death and art at the Stuart court. Book review.
Real estate, place adaptation and innovation.
Review and comment on the revised draft before July 11.
Write about something you know, help us build and grow !
A blended event and triumphant return.
Mark Reynolds succeeds Andy Mitchell as Co-Chair of CLC