- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Jul 2017
Heat interface unit
The BSRIA guide to heat interface units BG 62/2105 defines heat interface units (HIU sometimes referred to as ‘heat boxes’) as ‘…the means of connection of the consumer’s heating and hot water systems to a heat network and may include isolation and control valves, heat exchangers, pumps and metering devices.’
Traditionally in the UK, individual properties have been provided with their own heating systems, typically a boiler, providing domestic hot water (DHW) and central heating (CH). District heating provides heating to a group of buildings from central thermal energy generation plant via a network of fluid distribution pipes. It is widely used for residential, commercial, local authority, government, and industrial buildings as well as for universities and hospitals where there are a variety of discrete buildings located around a campus.
As greater attention has been paid to energy consumption and carbon emissions, so there is increasing interest in the use of district heat networks as a means of supplying heat more efficiently, particularly in multi-storey developments, where alternative, individual low-carbon technologies may be more difficult to instal.
Modern district heating systems generally use pressurised hot water for transferring heat from the central plant. Combined heat and power systems (CHP and sometimes called cogeneration), or other low-carbon technologies can be used for the central heat supply plant. CHP involves the local generation of electricity with the waste heat from the generation process being recovered and used in building heating systems or industrial processes. CHP is very energy efficient compared with traditional local generation of heat and import of electricity from large centrally-located electricity generation stations.
Heat interface units allow connection to a centralised heat network whilst still giving individual occupants control over the temperature in their property and allows individual metering and billing. They can provide heating only, or can provide heating and domestic hot water. BSRIA Guide BG 62/2105 suggests that installing a HIU linked to a heat network rather than a conventional boiler can have significant economic and environmental benefits, but that successful operation depends on appropriate system design and specification, and competent installation and maintenance.
There are a number of potential advantages to heat interface units:
- Central heat generation can be more efficient than local generation.
- It can be easier to integrate low carbon technologies.
- As local boilers are not required, there is no gas distribution network or flue requirement. This can result in both capital an operational cost savings.
- HIU’s can be installed outside of individual properties, giving easy access for landlords.
- They can allow remote monitoring and metering of consumption.
- They may allow a higher flow rate than domestic combination boilers.
Multi-zone systems may be provided for larger properties, and some systems may include a hot water cylinder. Typically, domestic how water supply is provided at around 75°C, and so if lower temperature water is required for a heating system such as underfloor heating , a mixing valve may be required. There may be hydraulic separation between the distribution network and the property, where distribution pressures may be high (such as in tall buildings) or to reduce the potential impact of leaks.
 Related articles on Designing Buildings Wiki
- A technical guide to district heating (FB 72).
- Allowable solutions.
- Biomass boiler.
- BSRIA guide to heat interface units
- CHP boiler.
- Combined heat and power.
- District energy networks
- Geothermal energy.
- Heat exchanger.
- Heat Networks Investment Project HNIP.
- Heat pump.
- Smart cities.
- Types of domestic boiler.
Featured articles and news
Dr Nicholas Falk, director of the URBED Trust, explains why metro cities are the future of urbanisation.
From next week, UK firms can bid for a share of a £12.5m fund to boost productivity, performance and quality.
A right to light generally refers to the right to receive sufficient light through an opening.
Interference and compatibility - the effects of electromagnetic fields in the workplace.
Important action is being taken to inspire young people to train as engineers.
A survey of Leicester’s historic buildings resulted in local listing being taken more seriously.
Demolition is the most high risk activity in the construction sector. Read our introductory article here.
BSRIA report on the domestic boiler market, with China recording the most 'dynamic market uptake'.
Do we really know everything important about the impacts of our infrastructure projects? And if we don’t, does it matter?
Former Chief executive Richard Howson blames government for being 'poor payers'.