- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 27 Apr 2018
Refrigerants in buildings
- For heating, ventilation and air conditioning (HVAC) systems.
- To provide cooling for refrigeration.
- To provide cooling for industrial processes.
They provide cooling in a process that is essentially the same as that used in domestic fridges, based on either compression or absorption:
In compression systems, a liquid refrigerant with a low boiling point absorbs heat from the body that is being cooled and boils in an evaporator to form a gas. The resulting gas is then compressed, which increases its temperature further. The gas is then condensed, releasing its latent heat which is rejected. The process then repeats.
Absorption refrigeration works on a similar basis, with a refrigerant that boils at low temperature and pressure, however, in this case, the refrigerant gas is then absorbed in a solution which is then heated in a ‘generator’ so that the refrigerant evaporates again, but this time at a higher pressure and temperature. The gas is then condensed, releasing its latent heat which is rejected. The process then repeats. See absorption refrigeration for more information.
Typically, in heating, ventilation and air conditioning systems, chiller units use refrigerants to produce chilled water that is piped to air handling units (or fan coil units) where it is used to cool the air that ventilates the building. The ‘warmed’ water is then returned to the chiller unit to be re-cooled.
An alternative system supplies the refrigerant itself (rather than chilled water) to terminal units supplying different thermal zones. These ‘variable refrigerant flow’ (VRF) systems use a single external condensing unit and multiple internal evaporators and can be more efficient, more compact and offer greater flexibility than other HVAC systems.
The exact opposite of the refrigeration process can be achieved by heat pumps, which use refrigerants, but reverse the cycle so that heat is supplied to the building rather than cooling. Some systems are reversible, able to supple either heat or cooling.
 CFC’s and HCFC’s
New equipment using HCFCs (hydrochlorofluorocarbons such as R22 and R408A) was banned in 2001 (2004 for small systems), and the use of virgin HCFC's was banned in 2010, when it also became illegal to manufacture HCFC refrigerants or for suppliers to keep them in stock.
From January 1st 2015 the use of HCFC’s was prohibited in any form, even for maintenance.
Refrigerants such as HFC's (hydrofluorocarbons) can often by used as drop-in replacements for HCFC’s however they can lead to a drop in efficiency and so may need to be supplemented with additional compressor and/or heat exchanger capacity. Badly maintained equipment or old HCFC systems may not lend themselves to conversion and could need complete replacement
Fluorinated gases (F gases) are not ozone depleting and they are often used as substitutes for CFC’s and HCFC’s. However they are powerful greenhouse gases (up to 20,000 times more powerful than CO2) and are listed as part of the Kyoto Protocol basket of greenhouse gases. As emissions of F gases increase, so their use is coming under greater scrutiny.
Other F gases include perfluorocarbons (PFCs) and sulphur hexafluoride (SF6).
On 15 October 2016 it was announced that 170 countries in Kigali, Rwanda, had agreed that all HFC’s should be phased out through an amendment to the Montreal Protocol. See HFC phase out for more information.
Other refrigerants include:
- Ammonia (R717). A so-called ‘natural’ refrigerant, commonly used in absorption refrigeration. Ammonia is not an ozone depleting gas or a global warming gas. However it is flammable and toxic so additional precautions are necessary in design and use.
- Non-halogenated hydrocarbons such as propane and butane (such as R290, R600a and R1270). These are ‘natural’ and not ozone depleting but do have some global warming potential and are flammable, so additional precautions are necessary in design and use.
- Carbon dioxide (R744). This is ‘natural’ and not ozone depleting but does have some global warming potential.
- Hydrofluoro olefin (HFO) is a refrigerant but is most commonly used in automotive air conditioning systems.
- Water and air.
It should be noted that refrigerants only have a global warming effect if they are allowed to leak to the atmosphere. This is more likely in ‘engineered’ systems than modular systems that have been hermetically sealed in the factory. Careful design, installation and maintenance can also help reduce leakage, and diagnostic and prognostic monitoring systems are available that can help detect or even predict leaks.
 Find out more
 Related articles on Designing Buildings Wiki
- Absorption refrigeration.
- Air conditioning.
- Air conditioning inspection.
- Air handling unit.
- BREEAM Impact of refrigerants.
- Chilled beam.
- Chiller unit.
- Chilled water.
- Cooling systems for buildings.
- Cooling tower design and construction.
- Compression refrigeration.
- Constant air volume.
- Evaporative cooling.
- Fan coil unit.
- Greenhouse gas.
- Latent heat.
- Montreal Protocol.
- Ozone depleting substance.
- Phase change.
- R22 phase out.
- Refrigeration market in Saudi Arabia
- Refrigerant selection.
- Variable refrigerant flow.
 External references
Featured articles and news
An artist finds ruined and decaying buildings a source of inspiration for his work. Book review.
When is there a right to light, and what happens if it is obstructed?
What would the nationalisation of economic infrastructure mean for GB?
A new guide to improving value by reducing design error.
We've reached 80,000 page views a day and 10,000 registered users. Why not join them?
A masterplan is a framework within which a location is encouraged to develop or change. Read our introductory article.
New consultation announced on a specialist Housing Court to settle landlord-tenant disputes.
ICE responds to a transport consultation advising the government to make decisions enabling more inclusive cities.
BRE and Loughborough University complete first phase refurbishment of demonstration home.
If you’re a great writer and have practical experience of the construction industry, it could be you.
Frustrated by long documents or technical jargon? Put off by sign-up forms or costs? Take this 5 min survey to help improve construction knowledge.