- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 24 Mar 2020
Designing HVAC to resist harmful pathogenic microorganisms (bacteria and viruses such as influenza and 2019-nCov)
The presence of airborne particles like dust, harmful pathogenic microorganisms like bacteria, viruses like influenza and 2019-nCov also known as Coronavirus is inevitable in occupied closed spaces/buildings. Heating Ventilation and Air Conditioning (HVAC) plays a vital role in making those buildings habitable. Other than providing comfort, it also affects the wellbeing of occupants by maintaining a healthy indoor environment.
One of the benefits of a well-designed HVAC system is control over harmful pathogenic microorganisms such as bacteria and viruses. Because of their harmful effects on health, wellbeing and indoor environments building owners must ensure these are kept under control. There are many methods to control those bacteria and viruses however this article will be discussing the following methods:
- Relative humidity control.
- Increased ventilation.
- Introducing high efficiency filters.
- UV lights in ducts.
It is possible to use these methods alone or in combination depending upon project requirements.
 Relative humidity control
The Centre of Disease Control and Prevention study states that “At humidity levels of 23 percent, 70 to 77 percent of the flu virus particles were still able to cause an infection an hour after the coughing simulation. But when humidity levels were raised to 43 percent, just 14 percent of the virus particles had the ability to infect. Most of the flu particles became inactive 15 minutes after they were released into the humid air. "The virus just falls apart," at high humidity levels.”
Though raising the humidity of the whole building is a challenge, it is highly recommended for the hospitals, clinics and the places where there is a high risk of flu transmission to consider increasing their humidity levels (30% - 40 %).
 Increased ventilation
As published by the Franunhofer Institute for Building Physics, people in industrialised countries spend 90% of their time indoors and as most of the air conditioning in those countries are of a recirculated type (with 20% fresh air addition only) to conserve energy, this results in an increased chance of airborne particles (harmful pathogenic microorganisms such as bacteria and viruses) staying longer in the space.
Ventilation can reduce the concentration of airborne pathogens through removing or diluting airborne droplet nuclei. A higher ventilation rate can provide a higher dilution capability and consequently, potentially reduce the risk of airborne infections.
This can be addressed by introducing additional ventilation (~40% instead of 20%) for high-risk areas. This is best done at the design stage, as once the building is constructed there is not much that can be done without breaking concrete and drilling holes in the walls and slab for duct installation.
 Introducing High Efficiency (HEPA) Filters
HEPA filters are high-efficiency particulate absorbing filters. A filter must remove 99.95% (EU standard) and 99.97% (ASME, US DOE) of 0.3 micrometers sized debris from the air that passes through it. The 2019-nCoV aka coronavirus being 50 to 200 nanometre in size cannot be filtered by traditional HEPA filters, and required manufacturers to produce special filters which can block smaller viruses.
Note: HEPA filters don’t kill viruses and bacteria and they can stay in the filter as long as they can survive (~9 days for 2019-nCoV). This brings us to our next design consideration of the introduction of UV Lights in AC ducts.
The presence of harmful pathogenic microorganisms such as viruses and bacteria in closed occupied spaces is inevitable and these microorganisms can be either killed by controlling the humidity of the space or can be pushed out by an increased (or doubled) ventilation. Since the buildings of today use a recirculating type ventilation system, the chances are that these organisms are either recirculating with the air, stuck to the AC duct walls or in the return air filter.
Introducing UV lamps in the return AC duct and near to the filter can have a significant effect on the indoor air quality by killing harmful viruses and resisting the growth of molds inside ducts. Since lamps prevent the build-up of particles both in the system and in the ducts, they also improve airflow and contribute to energy savings.
The four above mentioned methods / early design consideration will not only resist the harmful pathogenic microorganisms but will also improve indoor air quality which in turn can reduce operating costs of the AC system.
- High humidity for 20 minutes (This will kill the bacterial and viruses in the space).
- Increased ventilation (Will avoid mold making and will regulate the previously increased humidity).
- All of the intake fresh air and recirculating air passes through specially design HEPA filters.
- UV lights are installed inside the air ducts, preferably close to air filters to kill any residual bacteria and viruses
About the Author: Muhammad is an MEP consultant, LEED Green Associate and has years of experience in the design and development of commercial and residential buildings. He currently lives in Dubai and he loves to write about construction in general and MEP in particular.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air filtration and clean Indoor air quality standards.
- Budget 2020.
- Clean indoor air for healthy living - New air filter standards.
- Coronavirus and force majeure.
- Coronavirus impact survey.
- Coronavirus job retention scheme.
- Health effects of indoor air quality on children and young people.
Featured articles and news
Discover the Winchester Mystery House.
Priorities for rail in the Midlands and the North.
Examining renovate-operate-transfer arrangements.
Proactive measures to secure property during extreme times.
Safety guidance from BSI released; comments requested.
Scour can make river currents structurally damaging.
Indoor environmental quality looks at air quality and other wellbeing factors.
A procurement method associated with Public Private Partnerships.
Infrastructure can use digital technology to encourage human growth.
Robotics and the construction industry.
ECA comments on CLC's three-phase recovery plan.
Their diplomatic and architectural history.
The origins of the six volume series.
Built to defend British waters, only to serve as pirate radio stations later.
Wellbeing to influence mix of home and office based working.
An introduction to cobotics.