- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 18 Jan 2022
High efficiency particulate arrestance HEPA
High efficiency particulate arrestance, or HEPA, is a method of air filtration incorporated into a specific type of pleated mechanical particulate absorbing air filter. Due to the mechanical nature of their operations, HEPA purifiers are effective in environments where medical conditions such as asthma or allergies may be prevalent.
To qualify as a HEPA filter, the device must remove 99.95% (EU standard) or 99.97% (ASME, US DOE) of dust, pollen, mould, bacteria and airborne particles with a size of 0.3 microns (µm) from the air that passes through it. However, the term is sometimes used to market products that may not comply with this HEPA standard.
This value is used for filter classification because it is close to the most penetrating particle size (MPPS) of approximately 0.2-0.3 μm (NASA). Particles that are larger or smaller than the MPPS are filtered more efficiently than the rated efficiency, although in some circumstances particles below the MPPS may act as nucleation sites and form particles close to the MPPS.
HEPA filters first became available in the 1950s, but their effectiveness was not technically rated until after the introduction of the minimum efficiency reporting value (MERV) rating system. MERV was developed in the 1980s by the American Society of Heating, Refrigerating and Air-Conditioning Engineers (ASHRAE).
Using a range from 1 to 20, the MERV rating system reflects the measurement of a filter’s arrestance - or its ability to remove dust from the air - relative to how many of a specific size dust particle (within the range of 0.3 to 10 µm) need to be removed to keep HVAC equipment clean. The higher the MERV rating, the better the filter is at trapping specific types of particles.
In January 2009, ASHRAE stopped recognising general air filters with MERV values based on ratings in the 17 to 20 range. This range is instead represented by HEPA and ultra low particulate air (ULPA) filters, which are capable of removing extremely high levels of dust particles as well as some viruses and other dangerous airborne particulates.
 Proper care and operations of HEPA filters
Appropriate operating conditions are needed in order for HEPA filters to perform as designed. These parameters include velocity and direction of airflow, particle concentration, particle size distribution and appropriate temperature and humidity levels. Design factors, such as non-uniformity of filter pleats or improper filter installation, can also have an impact on the efficiency of these devices.
HEPA filters also need to be inspected and changed on a regular basis. The period between replacement may vary on the setting and the demands of the environment. If the filters are not maintained properly, they will no longer operate efficiently and may even have a negative impact on both the people and the equipment that they are meant to protect.
 HEPA filters and COVID-19
HEPA filters are not designed to kill viruses and bacteria, which can stay in the filter as long as they survive. This can be up to nine days for COVID-19 in certain conditions. However, COVID-19 survives best on hard surfaces and tends to die faster on soft, porous materials such as filter media.
- Air filtration.
- Air filtration and clean indoor air quality standards.
- American Society of Heating and Air-conditioning Engineers.
- Building ventilation and COVID-19 transmission risk.
- Clean indoor air for healthy living - New air filter standards.
- Designing HVAC to resist harmful microorganisms.
- Indoor air quality.
- Minimum efficiency reporting value MERV.
Featured articles and news
Meaning, understanding and implementation.
Kick-start attempts causes 50% jump from December.
From climate to cost to cold bridges and design flexibility.
In a changing world at the APM PM SIG conference.
The glass product that opened up new possibilities.
Campaigning for buildings of all periods.
Full life cycle assessments, impact categories and more.
Lansink's ladder to resin identification codes. Less is more.
Basic components in an increasingly complex material world.
Get to know the new requirements and the new terms.
Reporting on Payment Practices and Performance Regs.
Welcomed with a skills shortage warning.
The ultimate companion for building services excellence.
CIOB joins leading organisations to warn leaders.