- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 05 Jan 2017
Approved Document D
- What qualifies as 'building work' and so fall under the control of the regulations.
- What types of buildings are exempt.
- The notification procedures that must be followed when starting, carrying out, and completing building work.
- Requirements for specific aspects of building design and construction.
The 'approved documents' provide guidance for how the building regulations can be satisfied in common building situations. There is no obligation to adopt the solutions presented in the approved documents, the building regulations can be satisfied in other ways.
Part D of Schedule 1 to the Building Regulations requires that, 'If insulating material is inserted into a cavity in a cavity wall, reasonable precautions shall be taken to prevent the subsequent permeation of any toxic fumes from that material into any part of the building occupied by people.'
Approved Document D - Toxic Substances, provides guidance for complying with Part D. This relates the use of urea formaldehyde (UF) foam.
Approved document D suggests that '…insulating materials which give off formaldehyde fumes (either when used or later in normal use) may be used to insulate the cavity in a cavity wall where there is a continuous barrier which will minimise as far as practicable the passage of fumes to the occupiable parts.'
It provides the following technical solution:
A cavity wall may be insulated with UF foam where:
- the inner leaf of the wall is built of masonry (bricks or blocks); and
- the suitability of the wall for foam filling is assessed before the work is carried out in accordance with BS 8208-1:1985 Guide to assessment of suitability of external cavity walls for filling with thermal insulants. Existing traditional cavity construction; and
- the person carrying out the work holds (or operates under) a current Certificate of Registration of Assessed Capability for the work he is doing; and
- the material is in accordance with the relevant recommendations of BS 5617:1985 Specifications for urea formaldehyde (UF) foam systems suitable for thermal insulation of cavity walls with masonry or concrete inner and outer leaves; and
- the installation is in accordance with BS 5618:1985 Code of practice for thermal insulation of cavity walls (with masonry or concrete inner and outer leaves) by filling with urea formaldehyde (UF) foam systems.
 Find out more
 Related articles on Designing Buildings Wiki
- Approved documents.
- Approved document C
- Approved document G.
- Approved document L.
- Approved document M.
- Approved document P.
- Approved document Q.
- Approved inspector.
- Building control body.
- Building regulations.
- Cavity wall insulation.
- Northern Ireland building regulations.
- Scottish building standards.
- The Building Act.
- Welsh building regulations.
Featured articles and news
The built environment can unlock opportunities for skills.
Additionality is a concept applied to activities and projects.
Some HPL cladding is very unlikely to adequately resist the spread of fire.
What a chartered architectural technologist does.
Building design and construction fees.
The world heritage list has evolved to embrace built, cultural and natural heritage.
The Ocean Cleanup project
The various types of bond and when they are used.
It's vital the industry responds to proposals for reform of the safety regulatory system.
RSHP's Merano wins RIBA accolade.
How to differentiate between partial possession and early use.
Ofwat proposes £12 billion additional investment and £50 bill reductions.