Active thermal mass in buildings
To help develop this article, click ‘Edit this article’ above.
The term ‘thermal mass’ describes the ability of a material to absorb, store and release heat energy. Thermal mass can be used to even out variations in internal and external conditions, absorbing heat as temperatures rise and releasing it as they fall. In building design, this can useful for evening out and delaying extremes in thermal conditions, stabilising the internal environment and so reducing or eliminating the demand for building services systems. It can be beneficial both during the summer and the winter.
Thermal mass is often considered to be a passive component of environmental design, with heat transfer between the internal air of the building interior and the thermal mass by ‘natural’ convection. However, it can be difficult to achieve close temperature control with passive thermal mass, and large quantities of thermal mass can be required.
The term ‘active thermal mass’ refers to the controlled absorption and release of heat energy from thermal mass. This active control can be used to maximise heat transfer between thermal mass and internal spaces and to better tune the absorption and release of heat to heating and cooling demands.
Active thermal mass systems are generally air-based or fluid-based systems.
- Air-based systems operate by drawing ventilation air past the thermal mass at low velocity, to maximise the heat transfer with the air. This can be achieved by using the hollow core in pre-cast concrete slabs as a ventilation duct, or using the void created by raised floors as a supply plenum. Air-based systems can be used to regulate the temperature of the thermal mass during occupied periods and for night-time purging.
- Fluid-based systems typically pump water through pipes embedded in the floor slab (similar to underfloor heating piping) to moderate the temperature of the thermal mass. Water has a greater cooling potential than air, however, in this case, ventilation must be provided separately. The water temperature is generally maintained at above 14°C to avoid condensation, and it can also be used to provide heating in the winter.
Building management systems can be used to control active thermal mass systems based on internal and external temperatures, the temperature of the mass, the occupancy pattern of the building and any heating, ventilation and air conditioning (HVAC) systems.
 Related articles on Designing Buildings Wiki
Featured articles and news
Identifying sustainable shoreline protection solutions in the face of rising sea levels and storms in the US.
Budget documents state modern methods of construction will be favoured for public infrastructure schemes from 2019.
A walk-through exhibition of an emergency humanitarian shelter is officially opened at BRE's Innovation Park.
How to work safely on a construction site during winter.
Housing is the big winner in Chancellor Philip Hammond's Autumn Budget.
The winner of our BSRIA competition, Tomorrow's challenges in today's buildings, is.... Bob Hendrikx. A big thank you to everyone that took part.
Committee of MPs accuses government of dealing billpayers a 'bad hand' over the guaranteed power price.
In 1992, the Joint Fire Code was first published. What influence does it still have on construction sites today?
"Companies will have to adapt or go out of business" - how are virtual reality and big data disrupting digital construction?
International Well Building Institute and BRE collaborate on multiple levels to advance human health through better buildings.
"The industry has tried moving away from prescriptivism to focus on performance, but maybe that’s no longer working".
Energy from waste and its key role in a low carbon economy.
Sir Ranulph Fiennes was guest speaker at the BSRIA Briefing - Tomorrow’s challenges in today’s buildings.