Active thermal mass in buildings
To help develop this article, click ‘Edit this article’ above.
The term ‘thermal mass’ describes the ability of a material to absorb, store and release heat energy. Thermal mass can be used to even out variations in internal and external conditions, absorbing heat as temperatures rise and releasing it as they fall. In building design, this can useful for evening out and delaying extremes in thermal conditions, stabilising the internal environment and so reducing or eliminating the demand for building services systems. It can be beneficial both during the summer and the winter.
Thermal mass is often considered to be a passive component of environmental design, with heat transfer between the internal air of the building interior and the thermal mass by ‘natural’ convection. However, it can be difficult to achieve close temperature control with passive thermal mass, and large quantities of thermal mass can be required.
The term ‘active thermal mass’ refers to the controlled absorption and release of heat energy from thermal mass. This active control can be used to maximise heat transfer between thermal mass and internal spaces and to better tune the absorption and release of heat to heating and cooling demands.
Active thermal mass systems are generally air-based or fluid-based systems.
- Air-based systems operate by drawing ventilation air past the thermal mass at low velocity, to maximise the heat transfer with the air. This can be achieved by using the hollow core in pre-cast concrete slabs as a ventilation duct, or using the void created by raised floors as a supply plenum. Air-based systems can be used to regulate the temperature of the thermal mass during occupied periods and for night-time purging.
- Fluid-based systems typically pump water through pipes embedded in the floor slab (similar to underfloor heating piping) to moderate the temperature of the thermal mass. Water has a greater cooling potential than air, however, in this case, ventilation must be provided separately. The water temperature is generally maintained at above 14°C to avoid condensation, and it can also be used to provide heating in the winter.
Building management systems can be used to control active thermal mass systems based on internal and external temperatures, the temperature of the mass, the occupancy pattern of the building and any heating, ventilation and air conditioning (HVAC) systems.
 Related articles on Designing Buildings Wiki
Featured articles and news
Around 6,000 elephants were involved in the construction of the world's largest religious monument, Angkor Wat.
Government publishes new guidance document for landlords about the April 2018 changes.
ICE publish new briefing sheet on municipal energy transmission, retailing, and legislation.
CIOB awards include origami floor joists and BIM MOOC (Massive Open Online Course).
The first CIC briefing of 2017 covered a construction economic forecast, illegal migrant workers, and a Crossrail 2 update.
Have a look at this competition-winning proposal for a new mountain range-like complex in China.
BRE and Environment Agency join forces to try and build flood resilience into the fabric of Britain.
This spherical house in Vienna is considered a micro-nation - the Republic of Kugelmugel.
Commission has been awarded for a floating church designed after a pair of organ bellows.
"Teachers and schools do not understand construction very well" and need to do more, according to Carol Lynch.
ICE examine the use of structural engineering codes and the use of withdrawn British Standards.