Pipework defects, ventilation and airflow rates
The article originally appeared as Technical answers: Pipework defects, ventilation and airflow rates published in April 2016, written by Jayne Sunley, Information Manager at BSRIA.
 Foam insulation
Could foam insulation be the reason we are experiencing problems with pitting on copper pipework leading to leaks? The copper pipework in question is a chilled water service covered in phenolic foam which is only 4-5 years old. Could the vapour seal on the insulation be damaged leading to condensation forming on the pipe causing pitting and pin-holes?
In order to prove that insulation is the problem you need to establish with certainty that the perforations are from outside to inside and could not have been influenced by other sources of leakage such as weeping joints of previous pinholes. It would also be worth looking at the insulation manufacturer’s guidance to see whether it is the correct grade and has been applied properly. Sometimes there is a protective paper on the inside of the insulation that should not be removed, other manufacturers use an invisible coating or, for steel pipes, may recommend that a protective coating is applied to the pipe prior to installation.
Insulation on copper pipework is not a new issue but the European Phenolic Foam Manufacturers Association issued a statement in 2000 after an initial rash of problems.
 Stress fractures
Can stress fractures cause failure with ABS (Acrylonitrile Butadiene Styrene) and PVC pressure pipes?
Stress fractures are the most common defect and are caused by excessive application of adhesive and/or the application of mechanical stress to the joint prior to the adhesive fully curing. This often happens because the pipes and fittings to be connected are slightly misaligned but can be pushed together. A typical stress fracture is a longitudinal crack in the pipe, starting from inside the fitting, or at least near to the fitting. Longitudinal cracks in the middle of a length of pipe are more likely a consequence of impact damage or the pipe being dropped prior to installation.
Cracks may be not readily visible until water starts to appear. Once a crack is suspected then the methods applied by ANS using crack detection fluid can be useful to observe the extent of the crack. More detailed investigation requires the affected section is cut out and sectioned for microscopic examination of both the inside and outside surfaces. Further sections can then be cut to separate the material either side of the crack and examine the fracture surfaces.
 Ventilation air speed in ducting
There are no regulations in the UK about air velocities in ductwork, however there are recommendations. The BSRIA publication Rules of Thumb gives recommendations for different applications, for example in offices, 6.0 m/s in main ducts, and 5.5 m/s in branch ducts.
 Airflow rate of LED downlights
While airtightness is certainly a requirement of a dwelling or room, to the best of our knowledge there are no specific requirements or limits on individual light fittings. However, each penetration in the ceiling will provide a potential air leakage path and will add to the total leakage. As such, contractors may wish to be sure that if they install a significant number of light fittings they will not exceed the total permitted for the space.
Also, the better the light fitting the more leeway there may be for other items to leak while remaining within the overall total allowance. In practice, leakage through fittings will be very dependent on the ceiling material as well as the care of the fitter but leakage rates do give at least an initial baseline.
 Related articles on Designing Buildings Wiki:
Featured articles and news
How thermal comfort is quantified and how it can affect wellbeing.
Snøhetta complete a treehouse cabin that allows guests to lie beneath the Northern Lights.
Christiania is an anarchist 'freetown' in Copenhagen where strange and experimental architecture has flourished.
“UK waste data needs improving” say BRE specialists, in this summary of their report into construction waste.
UandI announce new joint venture with US developer to work on office refurbishment projects.
BSRIA give critical response to Theresa May's speech on leaving the EU.
Why buildings crack, how cracks are categorised and what can be done.
Inaugurated last week, the new Elbphilharmonie concert venue; a soaring new addition to Hamburg's skyline.
Summary of a new ICE Transport journal which says improving transport infrastructure is essential to eradicating global poverty.
BRE look at a new government report into the accuracy of heat meters.
Herzog & de Meuron get planning permission for revamp of Chelsea FC football stadium.