- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 14 Jan 2018
Fire doors in buildings
To help develop this article, click ‘Edit this article’ above.
Fire safety for building occupants is maintained through the provision of adequate means of escape in the event of a fire and by ensuring the fabric of a building does not contribute significantly to fire growth in the early stages following ignition.
A door or shutter, provided for the passage of persons, air or objects, which, together with its frame and furniture as installed in a building, is intended (when closed) to resist the passage of fire and/or gaseous products of combustion and is capable of meeting specified performance criteria to those ends. (It may have one or more leaves and the term includes a cover or other form of protection to an opening in a fire-resisting wall or floor, or in a structure surrounding a protected shaft.)
The performance required of fire doors in dwellinghouses is set out in Table B1 of Appendix B of Approved document B1, Fire Safety, Volume 1, Dwellinghouses.
- To maintain the integrity of means of escape in the event of a fire.
- To isolate areas within a building that represent a significant fire risk.
- To provide access through compartment walls.
Article 17 of The Regulatory Reform (Fire Safety) Order 2005 requires that a maintenance regime is established to ensure equipment such as fire doors are kept in an efficient state and Article 18 requires that the responsible person appoints competent person(s) to assist in undertaking preventive and protective measures. This includes ensuring fire resisting doors and escape doors are correctly installed and maintained, with inspections carried out every 6 months.
In 2015, on their third anniversary, the FDIS reported that 61% of fire doors inspected had problems with fire or smoke seals, nearly a quarter had unsuitable hinges and many fire doors had bigger gaps between the door and frame than the required 3mm.
 Related articles on Designing Buildings Wiki
- Automatic release mechanism.
- Fire compartment.
- Fire detection and alarm systems.
- Fire Door Inspection Scheme.
- Fire Doors (DG 524).
- Fire in buildings.
- Fire protection engineering.
- Fire resistance.
- Free-swing door closer.
- Hold-open device.
- Installing fire doors and doorsets (GG 86).
- Means of escape.
- Protected escape route.
- The Regulatory Reform (Fire Safety) Order 2005.
- Types of door.
- Self-closing device.
- Width of doors stairs and escape routes.
Featured articles and news
If events occur that cause the completion of the works to be delayed then these may be compensation events.
BSRIA's new Building MOTs Scheme is designed to provide guidance on the next steps after compliance.
At an ICE discussion, the focus was on delivering a Northern Infrastructure Strategy based on opportunity for all.
The Considerate Constructors Scheme officially launch the new Ultra Site status for contractors and supply chains.
The risk of specification errors in the cladding sector is "worryingly high" after Grenfell, according to major distributor.
Here is our outline work plan for a private sector design and build project.
BRE are to publish new guidance aimed at assuring buyers as to the merits of off-site construction methods.
Who are the various different stakeholders in development projects? Find out in our introductory article.
How a BRE office became the centre-piece for major biophilic design research.
A new interactive virtual experience allows visitors to explore ICE 200 exhibition from anywhere.