Fire doors in buildings
To help develop this article, click ‘Edit this article’ above.
Fire safety for building occupants is maintained through the provision of adequate means of escape in the event of a fire and by ensuring the fabric of a building does not contribute significantly to fire growth in the early stages following ignition.
A door or shutter, provided for the passage of persons, air or objects, which, together with its frame and furniture as installed in a building, is intended (when closed) to resist the passage of fire and/or gaseous products of combustion and is capable of meeting specified performance criteria to those ends. (It may have one or more leaves and the term includes a cover or other form of protection to an opening in a fire-resisting wall or floor, or in a structure surrounding a protected shaft.)
The performance required of fire doors in dwellinghouses is set out in Table B1 of Appendix B of Approved document B1, Fire Safety, Volume 1, Dwellinghouses.
- To maintain the integrity of means of escape in the event of a fire.
- To isolate areas within a building that represent a significant fire risk.
- To provide access through compartment walls.
Article 17 of The Regulatory Reform (Fire Safety) Order 2005 requires that a maintenance regime is established to ensure equipment such as fire doors are kept in an efficient state and Article 18 requires that the responsible person appoints competent person(s) to assist in undertaking preventive and protective measures. This includes ensuring fire resisting doors and escape doors are correctly installed and maintained, with inspections carried out every 6 months.
In 2015, on their third anniversary, the FDIS reported that 61% of fire doors inspected had problems with fire or smoke seals, nearly a quarter had unsuitable hinges and many fire doors had bigger gaps between the door and frame than the required 3mm.
 Related articles on Designing Buildings Wiki
- Automatic release mechanism.
- Controlled fitting.
- Door energy rating.
- Door closer.
- Door terminology.
- Escape route.
- Fire compartment.
- Fire detection and alarm systems.
- Fire Door Inspection Scheme.
- Fire in buildings.
- Fire Prevention on Construction Sites.
- Fire protection engineering.
- Fire resistance.
- Firefighting lobby.
- Free-swing door closer.
- Hold-open device.
- How the substrate affects external timber doors.
- Inner room.
- Installing fire doors and doorsets (GG 86).
- Joint fire code.
- Means of escape.
- Protected escape route.
- The Regulatory Reform (Fire Safety) Order 2005.
- Unprotected escape route.
- Self-closing device.
- Visual alarm devices - their effectiveness in warning of fire.
- Width of doors stairs and escape routes.
Featured articles and news
We interviewed the photographer Jade Doskow about her new book documenting the strange architecture of World's Fair sites.
Industry leaders join CIOB and Stronger Together to tackle modern slavery in construction.
Drawing on the recent Mexico earthquake, a collection of free journal articles has been assembled.
Read this introductory article to the base date in construction contracts.
Why is this American teapot-shaped gas station historically significant? Find out here.
Plans for the first phase of Vastint’s 16.5-acre Tetley Brewery development project get the green light.
This article explores the question, how should we regulate the real estate industry?
Specialist regeneration and investment developer UandI announces ambitions with new Manchester office.
Concrete will have to be demolished and replaced in Hinkley Point tunnels.
Do you have a great idea for how tomorrow's challenges can be met by today's buildings? Enter our ideas competition today.
A new exhibition on humanitarian shelter design will open on BRE's Innovation Park next month.
ICE London Air Quality Taskforce launches plan to help clean up London’s polluted air.
From neolithic to neo-modernism, have a read of our summary of the main architectural styles.