- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 07 Feb 2018
A consumer unit is defined by BS 7671:2008+A3:2015, the IET Wiring Regulations, as “a particular type of distribution board comprising a type-tested co-ordinated assembly for the control and distribution of electrical energy, principally in domestic premises, incorporating manual means of double-pole isolation on the incoming circuit(s) and an assembly of one or more fuses, circuit-breakers, residual current operated devices, or signalling and other devices proven during the type-test of the assembly as suitable for such use.” A consumer unit may also be known as a consumer control unit or electricity control unit and may often still be referred to as a fuse box (old term).
A consumer unit ordinarily controls and distributes power to electrical accessories and equipment in a dwelling, including circuits for socket-outlets, lighting circuits, cookers, showers and anything else that requires an electrical supply. It is common for modern consumer units either to have:
- individual residual current circuit-breakers with overcurrent protection (RCBOs) for each circuit; or
- a split load system where two or more residual current circuit-breakers (RCCB) each protects a group of circuits. Should one RCCB operate, other circuits would remain live.
Consumer units installed in the UK must also meet the requirements of Regulation 132.12 Accessibility of electrical equipment, e.g. where disabled persons would access the consumer unit in order to reset circuit-breakers, RCCBs or RCBOs.
New regulation 421.1.201
In January 2015, Amendment No 3 to BS 7671:2008 introduced a regulation relating to consumer units. The wording of that regulation is as follows:
421.1.201 Within domestic (household) premises, consumer units and similar switchgear assemblies shall comply with BS EN 61439-3 and shall:
(i) have their enclosure manufactured from non-combustible material, or
(ii) be enclosed in a cabinet or enclosure constructed of non-combustible material and complying with Regulation 132.12.
NOTE 1: Ferrous metal, e.g. steel, is deemed to be an example of a non-combustible material.
NOTE 2: The implementation date for this regulation is the 1st January 2016, but does not preclude compliance with the regulation prior to that date.
The implementation date for this new regulation was 1 January 2016.
The intent behind the new regulation was to contain, as far as is reasonably practicable, any fire within the enclosure or cabinet and to minimise the escape of flames.
Find out more
- IET magazine Wiring Matters publishes industry articles for electricians and installers. The related blog published an updated article about consumer units in January 2016
Featured articles and news
Starting a new built environment degree? We have a wide range of resources aimed at students.
Former railway chief James Blake says trust and control are key to successful infrastructure projects.
Do you know your Rococo from your De Stijl, your Gothic from your Post-modernist?
May outlines a new funding strategy for housing associations and says the 'stigma' of social housing needs to end.
RIBA launches a consultation on a new Plan of Work for Fire Safety.
This article offers some basic rules to follow when writing your next specification.
The iconic Mackintosh Building will definitely be rebuilt, board chairwoman confirms.
The machinery used to fashion stone has changed dramatically - and so have the products.
This type of pile provides support to the building, as well as acting as a heat source and a heat sink.
Why investors are adopting the SDGs and why civil engineering could be crucial for delivering them.
Read about all the winners from the London ceremony of CIAT's 2018 Architectural Technology Awards.