- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 07 Feb 2018
A consumer unit is defined by BS 7671:2008+A3:2015, the IET Wiring Regulations, as “a particular type of distribution board comprising a type-tested co-ordinated assembly for the control and distribution of electrical energy, principally in domestic premises, incorporating manual means of double-pole isolation on the incoming circuit(s) and an assembly of one or more fuses, circuit-breakers, residual current operated devices, or signalling and other devices proven during the type-test of the assembly as suitable for such use.” A consumer unit may also be known as a consumer control unit or electricity control unit and may often still be referred to as a fuse box (old term).
A consumer unit ordinarily controls and distributes power to electrical accessories and equipment in a dwelling, including circuits for socket-outlets, lighting circuits, cookers, showers and anything else that requires an electrical supply. It is common for modern consumer units either to have:
- individual residual current circuit-breakers with overcurrent protection (RCBOs) for each circuit; or
- a split load system where two or more residual current circuit-breakers (RCCB) each protects a group of circuits. Should one RCCB operate, other circuits would remain live.
Consumer units installed in the UK must also meet the requirements of Regulation 132.12 Accessibility of electrical equipment, e.g. where disabled persons would access the consumer unit in order to reset circuit-breakers, RCCBs or RCBOs.
New regulation 421.1.201
In January 2015, Amendment No 3 to BS 7671:2008 introduced a regulation relating to consumer units. The wording of that regulation is as follows:
421.1.201 Within domestic (household) premises, consumer units and similar switchgear assemblies shall comply with BS EN 61439-3 and shall:
(i) have their enclosure manufactured from non-combustible material, or
(ii) be enclosed in a cabinet or enclosure constructed of non-combustible material and complying with Regulation 132.12.
NOTE 1: Ferrous metal, e.g. steel, is deemed to be an example of a non-combustible material.
NOTE 2: The implementation date for this regulation is the 1st January 2016, but does not preclude compliance with the regulation prior to that date.
The implementation date for this new regulation was 1 January 2016.
The intent behind the new regulation was to contain, as far as is reasonably practicable, any fire within the enclosure or cabinet and to minimise the escape of flames.
Find out more
- IET magazine Wiring Matters publishes industry articles for electricians and installers. The related blog published an updated article about consumer units in January 2016
Featured articles and news
This article examines the changing policy commitments and evolving definitions of the zero carbon home.
Researchers believe they may have created a 'game-changing' new form of concrete using graphene.
Grouting refers to the injection of materials into a soil or rock formation to change its physical characteristics.
Part of Designing Buildings Wiki, BREEAM Wiki will advance knowledge sharing for the BRE family of sustainability tools.
From the decorative to the utilitarian, and from the photographed to the forgotten.
New BRE book considers the progression from project-based knowledge creation to whole-life urban knowledge management.
This CIOB article explores the concept of value in building design and construction.
BREEAM and Measurabl announce integration to improve the financial performance of commercial real estate.
Rogers Stirk Harbour + Partners' release new images of soon-to-open 3WTC tower in New York.
A document can be called a bond or a guarantee. Does the name matter and what is the difference between them?
New briefing note is launched focusing on increasing knowledge of housing that promotes health and wellbeing.
Arbitration is a private, contractual form of dispute resolution used in the construction industry.