A consumer unit is defined by BS 7671:2008+A3:2015, the IET Wiring Regulations, as “a particular type of distribution board comprising a type-tested co-ordinated assembly for the control and distribution of electrical energy, principally in domestic premises, incorporating manual means of double-pole isolation on the incoming circuit(s) and an assembly of one or more fuses, circuit-breakers, residual current operated devices, or signalling and other devices proven during the type-test of the assembly as suitable for such use.” A consumer unit may also be known as a consumer control unit or electricity control unit and may often still be referred to as a fuse box (old term).
A consumer unit ordinarily controls and distributes power to electrical accessories and equipment in a dwelling, including circuits for socket-outlets, lighting circuits, cookers, showers and anything else that requires an electrical supply. It is common for modern consumer units either to have:
- individual residual current circuit-breakers with overcurrent protection (RCBOs) for each circuit; or
- a split load system where two or more residual current circuit-breakers (RCCB) each protects a group of circuits. Should one RCCB operate, other circuits would remain live.
Consumer units installed in the UK must also meet the requirements of Regulation 132.12 Accessibility of electrical equipment, e.g. where disabled persons would access the consumer unit in order to reset circuit-breakers, RCCBs or RCBOs.
New regulation 421.1.201
In January 2015, Amendment No 3 to BS 7671:2008 introduced a regulation relating to consumer units. The wording of that regulation is as follows:
421.1.201 Within domestic (household) premises, consumer units and similar switchgear assemblies shall comply with BS EN 61439-3 and shall:
(i) have their enclosure manufactured from non-combustible material, or
(ii) be enclosed in a cabinet or enclosure constructed of non-combustible material and complying with Regulation 132.12.
NOTE 1: Ferrous metal, e.g. steel, is deemed to be an example of a non-combustible material.
NOTE 2: The implementation date for this regulation is the 1st January 2016, but does not preclude compliance with the regulation prior to that date.
The implementation date for this new regulation was 1 January 2016.
The intent behind the new regulation was to contain, as far as is reasonably practicable, any fire within the enclosure or cabinet and to minimise the escape of flames.
Find out more
Featured articles and news
Have a look at our article explaining the different types of construction contractor.
Futurist Thomas Frey explores the concept of Disposable Housing - could it be a reality sooner than we imagine?
ICE to host new exhibition offering a window onto the civil engineering achievements beneath our feet.
Do you know all the various types of defects in brickwork?
US museum reveals plans for an installation made entirely of paper tubes.
Review of a book looking at how contemporary architecture found its expression within neoliberal capitalism.
The Great Mosque of Djenne, the largest mud-brick building in the world.
Amanda Clack, RICS President offers recommendations to government on Brexit and the construction skills shortage.
Tired of the commute? This architecture firm believes the best solution is to take cars underground.
Why do so many women leave engineering? Probably not for the reason you’re thinking.
For over 30 years David Trench was one of the UK's leading project managers. Read about his career through some of his most famous projects.
Leading institutes join forces calling for property flood resilience measures to help householders avoid repeat flooding.