- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 28 Dec 2020
Residual current device
Residual current devices (RCDs) are: ‘...designed to break an electrical current very easily by detecting any abnormality in the circuit, for example, through someone touching a live wire. They are normally located in the consumer unit but a separate RCD may exist to protect an additional circuit, for example, an electrical circuit used in the garden.’
Ref English Housing Survey, Profile and condition of the English housing stock, 2018-19, Published by the Ministry of Housing, Communities & Local Government in August 2020 suggests:
 Related articles on Designing Buildings Wiki
- Articles about electricity.
- ECA articles.
- Electrical appliance.
- Electrical consumption.
- Electrical energy.
- Electrical equipment.
- Electrical installation.
- Electrical power.
- Electrical safety.
- Electricity bill.
- Fuse box.
- Glossary of electrical terms.
- Miniature circuit breaker.
- Fuse box.
Featured articles and news
Exploring the key to the adoption of this abundant energy source.
His clients have ranged from Liberace to St Nick to world-class athletes.
These tactical structures can be permanent or temporary.
Organisation recognises milestones of the project's next phase.
Welding and metalworking businesses must manage respiratory risks.
New report explores how regulations are being put into action.
The golden thread and BS 8644-1.
Bitumen binder may delay road surface deterioration.
A varied portfolio of internationally recognised buildings.
Threatened by housing and expanding universities.
Getting "boots on the ground" to make things happen.
Building systems may begin to learn.
CIOB to recognise Client of the Year and Team of the Year.
PAS 9980 PAS 9980:2021 addresses fire risk appraisal and assessment.