- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 14 Aug 2020
Residual current device
Residual current devices (RCDs) are: ‘...designed to break an electrical current very easily by detecting any abnormality in the circuit, for example, through someone touching a live wire. They are normally located in the consumer unit but a separate RCD may exist to protect an additional circuit, for example, an electrical circuit used in the garden.’
Ref English Housing Survey, Profile and condition of the English housing stock, 2018-19, Published by the Ministry of Housing, Communities & Local Government in August 2020 suggests:
 Related articles on Designing Buildings Wiki
- Articles about electricity.
- ECA articles.
- Electrical appliance.
- Electrical consumption.
- Electrical energy.
- Electrical equipment.
- Electrical installation.
- Electrical power.
- Electrical safety.
- Electricity bill.
- Fuse box.
- Glossary of electrical terms.
- Miniature circuit breaker.
- Fuse box.
Featured articles and news
Eight forms of resource optimisation.
CIOB responds to Chancellor Sunak's announcement on jobs and the economy.
Revised guide to competition rules available.
Brick slip soffit systems and intricate brick features.
An innovative engineering approach could have had tragic consequence for NYC.
Some secrets behind how canals work.
Breaking down possible steps of pre-contract management.
ICE event includes comments from Welsh Government Minister Julie James.
How to write them and what they should include.
Designing Buildings Wiki becomes the world's first website to adopt the new knowledge standard.
Assessing the most beneficial design elements.
Exploring different types of vinyl flooring.