Thermal bridging in buildings
A thermal bridge (sometimes referred to as thermal bridging, a cold bridge or thermal bypass) describes a situation in a building where there is a direct connection between the inside and outside through one or more elements that are more thermally conductive than the rest of the building envelope.
As a result, there will be wasteful heat transfer across this element, its internal surface temperature will be different from other, better insulated internal surfaces and there may be condensation where warm, moist internal air comes into contact with the, potentially cold, surface. This condensation can result in mould growth.
In modern buildings, thermal bridging can occur because of poor design, or poor workmanship. This is common where elements of the building penetrate through its insulated fabric, for example around glazing, or where the structure penetrates the building envelope, such as at balconies.
However, as buildings have become better insulated, with increasingly strict regulation, so thermal bridges that might previously have been considered insignificant in terms of the overall thermal performance of a building, can actually be the cause of considerable thermal inefficiency. There is the potential for such inefficiency at every opening and every junction (even in party walls).
The Approved Documents to Part L of the building regulations (Conservation of fuel and power) state that 'The building fabric should be constructed so that there are no reasonably avoidable thermal bridges in the insulation layers caused by gaps within the various elements, at the joints between elements and at the edges of elements such as those around window and door openings.'
They require that where unaccredited construction details are used, generic linear thermal bridge values must be increased by levels (depending on the building type) set out in the Approved Documents for the calculations of building emission rates (BER) or dwelling emission rates (DER).
Thermal bridges in completed buildings can be revealed with thermal imaging cameras (see Thermographic survey), but they can be very difficult to rectify, particularly if they are repeated throughout a building.
 Related articles on Designing Buildings Wiki
- Accredited construction details ACDs.
- Air tightness in buildings.
- Building fabric.
- Cavity wall.
- Co-heating test.
- Computational fluid dynamics.
- Conventions for calculating linear thermal transmittance and temperature factors.
- Defects in dot and dab.
- Emission rates in the building regulations.
- Floor insulation.
- Insulation for ground floors.
- Insulation specification.
- Interstitial condensation.
- Mould growth.
- Rising damp.
- Roof insulation.
- Solid wall insulation.
- Thermal comfort.
- Thermographic survey.
Featured articles and news
What is liquidation and how does it apply to contractors in the construction industry?
Scrutiny is placed on Carillion's controversial 2013 decision to extend subcontractor payment terms to 120 days.
RSHP unveil their involvement in a boundary crossing which will provide a new entry point into Hong Kong.
With PFI currently under the spotlight due to Carillion, this introductory article explains what they are.
Estimates suggest that up to 30,000 small firms could be at risk of non-payment as a result of Carillion's collapse.
Sir Oliver Letwin to lead an independent review into the delays in the delivery of housing.
As Carillion collapses, read our article explaining insolvency in the construction industry.
43,000 jobs at risk as Carillion declares insolvency..
1961 saw the publication of three important books about urban design that remain relevant today.
Next week the planning fee increases by 20% and new fees are introduced.
How the transformative power of BIM and other digital technologies can be used to gain a competitive edge.