- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 05 Jul 2016
There is significant evidence to suggest that buildings do not perform as well when they are completed as was anticipated when they were being designed. The difference between anticipated and actual performance is known as the performance gap.
The co-heating test is used to measure the amount of heat lost through the thermal envelope of completed buildings. It provides an assessment of the as-built performance of whole buildings, that is, their heat loss coefficient (HLC). It is calculated by comparing the heat input into a building against the disparity between temperatures inside and outside the building.
The test measures the heat that is lost through the elements of the building fabric such as walls, floor, roof, doors, windows, and so on. Comparing this to the heat loss that was expected during the design process (such as heat loss calculated for the Standard Assessment Procedure (SAP)) can identify problems and help improve the design of buildings in the future.
The test is carried out after the completion of a new-build or refurbishment project, but before it is occupied. It involves heating the building to a constant internal temperature, usually 25°C, over a period of time, typically 1 to 3 weeks. This constant temperature is achieved by using fan-assisted convector heaters with further fan assistance to ensure good air mixing so that there is an even temperature throughout the building. An integral and differential controller linked to temperature sensors is used to maintain the temperature to ±0.2°C.
During the test the building should remain unoccupied and any equipment that may use or generate energy should be switched off. Plotting the daily heat input against the daily difference in temperature between interior and exterior, indicates the heat loss coefficient as a static value in W/K.
For optimum testing, with an internal temperature of 25°C, there should be a temperature difference of at least 10°C between the interior and exterior, which is why tests tend to be carried out over winter months between October and April. This also helps mitigate against the impact of solar gain which requires a correction to be applied.
Co-heating testing may be beneficial where buildings are representative of standard types to be replicated on a larger scale with improvements made in response to the test's findings, or where different construction or contracting methods need to be compared.
The testing may not be suitable where buildings have not been able to dry out for several months before testing, where buildings are apartments or multi-use, or where buildings are bespoke designs that are not going to be replicated.
There has been some criticism of the test as it requires that buildings are undisturbed and unoccupied for a long period of time, and because of the potential impact of external weather conditions and in particular solar radiation on the results.
 Find out more
 Related articles on Designing Buildings Wiki
- Building heating systems.
- Building performance evaluation.
- Building performance metrics.
- Cold bridge.
- Heat transfer.
- Performance gap.
- Radiant heating.
- Standard assessment procedure.
- Thermal comfort.
- U value.
 External references
- BPE Guide - Co-heating tests
- Open Energy Monitor - Measuring thermal performance
Featured articles and news
When is there a right to light, and what happens if it is obstructed?
What would the nationalisation of economic infrastructure mean for GB?
A new guide to improving value by reducing design error.
We've reached 80,000 page views a day and 10,000 registered users. Why not join them?
A masterplan is a framework within which a location is encouraged to develop or change. Read our introductory article.
New consultation announced on a specialist Housing Court to settle landlord-tenant disputes.
ICE responds to a transport consultation advising the government to make decisions enabling more inclusive cities.
BRE and Loughborough University complete first phase refurbishment of demonstration home.
How the risk of collapse of fibrous plaster ceilings is being addressed in theatres.
If you’re a great writer and have practical experience of the construction industry, it could be you.
Frustrated by long documents or technical jargon? Put off by sign-up forms or costs? Take this 5 min survey to help improve construction knowledge.