- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Nov 2020
There is significant evidence to suggest that buildings do not perform as well when they are completed as was anticipated when they were being designed. The difference between anticipated and actual performance is known as the performance gap.
The co-heating test is used to measure the amount of heat lost through the thermal envelope of completed buildings. It provides an assessment of the as-built performance of whole buildings, that is, their heat loss coefficient (HLC). It is calculated by comparing the heat input into a building against the disparity between temperatures inside and outside the building.
The test measures the heat that is lost through the elements of the building fabric such as walls, floor, roof, doors, windows, and so on. Comparing this to the heat loss that was expected during the design process (such as heat loss calculated for the Standard Assessment Procedure (SAP)) can identify problems and help improve the design of buildings in the future.
The test is carried out after the completion of a new-build or refurbishment project, but before it is occupied. It involves heating the building to a constant internal temperature, usually 25°C, over a period of time, typically 1 to 3 weeks. This constant temperature is achieved by using fan-assisted convector heaters with further fan assistance to ensure good air mixing so that there is an even temperature throughout the building. An integral and differential controller linked to temperature sensors is used to maintain the temperature to ±0.2°C.
During the test the building should remain unoccupied and any equipment that may use or generate energy should be switched off. Plotting the daily heat input against the daily difference in temperature between interior and exterior, indicates the heat loss coefficient as a static value in W/K.
For optimum testing, with an internal temperature of 25°C, there should be a temperature difference of at least 10°C between the interior and exterior, which is why tests tend to be carried out over winter months between October and April. This also helps mitigate against the impact of solar gain which requires a correction to be applied.
Co-heating testing may be beneficial where buildings are representative of standard types to be replicated on a larger scale with improvements made in response to the test's findings, or where different construction or contracting methods need to be compared.
The testing may not be suitable where buildings have not been able to dry out for several months before testing, where buildings are apartments or multi-use, or where buildings are bespoke designs that are not going to be replicated.
There has been some criticism of the test as it requires that buildings are undisturbed and unoccupied for a long period of time, and because of the potential impact of external weather conditions and in particular solar radiation on the results.
 Related articles on Designing Buildings Wiki
- Building heating systems.
- Building performance evaluation.
- Building performance metrics.
- Cold bridge.
- Heat transfer.
- Performance gap.
- Radiant heating.
- Standard assessment procedure.
- Thermal comfort.
- U value.
 External references
Featured articles and news
Prioritising tax considerations.
The four D creative process: discover, define, develop and deliver.
National Cyber Security Centre initiative is announced.
Reviewing trends and projections.
Legislation will establish initiatives to move towards net zero.
How to document contractor employment status.
Tech tools to help manage people and space post-pandemic.
A style that ranges from mock Tudor to arts and crafts to the 'Wrenaissance'.
Free guide from Secured by Design.
BREEAM strategy for sustainability and the circular economy.
Free tool to improve the construction programming process.
Are buildings doing what they're supposed to be doing?
Cities with quick access to everything by foot or bike.
The pressures and pinch points of global destinations.