- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 02 Sep 2020
Drying room - Scotland
Drying washing indoors can produce large amounts of water vapour that needs to be removed before it can damage the building fabric or generate mould growth that can be a risk to the health of occupants.
From 1963 to 1986 the building regulations included a requirement for the provision of drying facilities. This was removed in response to increased ownership of specialised appliances and the vandalism of common drying areas in blocks of flats.
The current Scottish Technical Standards, require, where reasonably practicable, an accessible outdoor space for drying laundry of at least 1.7 m of clothes line, and a designated internal space of at least 1 m3, allowing 1.7 m of clothes line.
The designated space may be either:
- Capable of allowing a wall mounted appliance which may, for example be fixed over a bath, or
- Capable of allowing a ceiling-mounted pulley arrangement, or
- A floor space in the dwelling on which to set out a clothes horse.
Normally a utility room or bathroom is used and mechanical extract is the usual method of removing moisture. Where a space other than a utility room or bathroom is designated, that space should be provided with either:
- Mechanical extraction capable of at least 15 l/s intermittent operation. The fan should be connected through a humidistat set to activate when the relative humidity is between 50 and 65%, or
- A passive stack ventilation system.
However, in 2011, the ‘Design Guide: Healthy Low Energy Home Laundering’, published by the Mackintosh School of Architecture, found that drying laundry in the home posed a health risk to people prone to conditions such as asthma and hay fever.
The report pointed out that 1.7m of clothes line was an inadequate length, and highlighted the fact that the indoor space is not required to be an enclosed dedicated space – a drying room. This means there can be migration of moisture to the rest of the home.
Surveys conducted by the researchers illustrated that residents used convenient drying cupboards when they were provided in a property. However, it was found that drying cupboards had become redundant in many cases, with the removal of a means of extracting air. The report stated that, with appropriate guidance, such spaces could be ‘reactivated’ in existing homes, as well as be designed into new housing.
The researchers recommended that an independently heated and ventilated drying room or cupboard could be located within a bathroom, or other room or circulation space, such as a landing. They recommended the provision of a space capable of accommodating a typical washing load with a minimum net volume of 1.75 m3.
The following dimensional options were provided:
- 1.75 m3 cupboard: 2.3 m high x 0.9 m wide x 0.85 m deep.
- Defined space within a larger utility room: 2.1 m long x 1.5 m deep x 2.3 m high.
- Double-tier vertical hanging space within tighter utility volume: For example, 1.75 m long x 1.5 m deep x 2.3 m high.
The report recommended that a drying room/cupboard should be connected to a house’s central heating system, and ideally, the drying room should have its own heat source capable of being independently operated from the primary heating system, to avoid residents having to turn on the whole heating system to dry laundry.
 Related articles on Designing Buildings Wiki
- Mud room.
- Scottish building services certification schemes.
- Scottish building standards.
- Scottish planning policy.
- Stack effect.
- Utility room definition.
- Home Laundry Study - Design report
Featured articles and news
Standard will help employers foster wellbeing and manage psychosocial risks.
Global fire standards for safety of people and property.
An introduction to the 5 core principles of lean.
Can the profession use its skills to save the world from climate change?
How faulty science resulted in sanitation reform.
Improving facilities, accessibility and overall appearance.
Free download of TG 12/2021 available.
TESP works with The Youth Group to form skill sharing network.
Big tech collaborates on platform for the built environment.
Letter signed by 21 organisations sent to MHCLG.
A look at the Government's strategic approach.
Steps to help reduce the spread of infection inside buildings.
This social media-centred hobby can be both dangerous and illegal.
Millwork wall treatment with a long and illustrious history.
Click the button to subscribe.