Drying room - Scotland
Drying washing indoors can produce large amounts of water vapour that needs to be
From 1963 to 1986 the building regulations included a requirement for the provision of drying facilities. This was removed in response to increased ownership of specialised appliances and the vandalism of common drying areas in blocks of flats.
The current Scottish Technical Standards, require, where reasonably practicable, an accessible outdoor space for drying laundry of at least 1.7 m of clothes line, and a designated internal space of at least 1 m3, allowing 1.7 m of clothes line.
The re-introduction of space to allow washing to be dried other than by a tumble drier was
The designated space may be either:
- Capable of allowing a wall mounted appliance which may, for example be fixed over a bath, or
- Capable of allowing a ceiling-mounted pulley arrangement, or
- A floor space in the dwelling on which to set out a clothes horse.
Normally a utility room or bathroom is used and mechanical extract is the usual method of removing moisture. Where a space other than a utility room or bathroom is designated, that space should be provided with either:
- Mechanical extraction capable of at least 15 l/s intermittent operation. The fan should be connected through a humidistat set to activate when the relative humidity is between 50 and 65%, or
- A passive stack ventilation system.
However, in 2011, the ‘Design Guide: Healthy Low Energy Home Laundering’, published by the Mackintosh School of Architecture, found that drying laundry in the home posed a health risk to people prone to conditions such as asthma and hay fever.
The report pointed out that 1.7m of clothes line was an inadequate length, and highlighted the fact that the indoor space is not required to be an enclosed dedicated space – a drying room. This means there can be migration of moisture to the rest of the home.
Surveys conducted by the researchers illustrated that residents used convenient drying cupboards when they were provided in a property. However, it was found that drying cupboards had become redundant in many cases, with the removal of a means of extracting air. The report stated that, with appropriate guidance, such spaces could be ‘reactivated’ in existing homes, as well as be designed into new housing.
The researchers recommended that an independently heated and ventilated drying room or cupboard could be located within a bathroom, or other room or circulation space, such as a landing. They recommended the provision of a space capable of accommodating a typical washing load with a minimum net volume of 1.75 m3.
The following dimensional options were provided:
- 1.75 m3 cupboard: 2.3 m high x 0.9 m wide x 0.85 m deep.
- Defined space within a larger utility room: 2.1 m long x 1.5 m deep x 2.3 m high.
- Double-tier vertical hanging space within tighter utility volume: For example, 1.75 m long x 1.5 m deep x 2.3 m high.
The report recommended that a drying room/cupboard should be connected to a house’s central heating system, and ideally, the drying room should have its own heat source capable of being independently operated from the primary heating system, to avoid residents having to turn on the whole heating system to dry laundry.
 Related articles on Designing Buildings Wiki
- Scottish building services certification schemes.
- Scottish building standards.
- Scottish planning policy.
- Stack effect.
- Utility room definition.
 External resources
Featured articles and news
High quality and high density homes - is it what we need or is it storing up trouble?
Government announces its intention to strengthen planning rules to protect music venues and neighbours.
National Audit Office reports that there is little evidence that PFI offers better value than other forms of contracting.
What is liquidation and how does it apply to contractors in the construction industry?
Scrutiny is placed on Carillion's controversial 2013 decision to extend subcontractor payment terms to 120 days.
RSHP unveil their involvement in a boundary crossing which will provide a new entry point into Hong Kong.
With PFI currently under the spotlight due to Carillion, this introductory article explains what they are.
Estimates suggest that up to 30,000 small firms could be at risk of non-payment as a result of Carillion's collapse.
Sir Oliver Letwin to lead an independent review into the delays in the delivery of housing.
As Carillion collapses, read our article explaining insolvency in the construction industry.
43,000 jobs at risk as Carillion declares insolvency.