Heating ventilation and air conditioning HVAC
It is sometimes extended to include refrigeration (HVACR), for example in CIBSE Guide B. Heating, Ventilating, Air Conditioning and Refrigeration.
- Internal air quality can be maintained by a combination of introducing 'fresh' air into the building, extracting 'stale air' and by filtration. Ventilation may be natural, mechanical, or mixed mode (a hybrid system). See ventilation form more information.
- Internal temperatures can be regulated by heating and cooling. Typically this is achieved by heated water (or sometimes steam) and chilled water that is generated by boilers and chillers and then used in heating coils and cooling coils as part of the ventilation system. Alternatively hot water may be used to supply radiators.
- Humidity can be regulated by ventilation, dehumidification and humidification. Dehumidification is often provided alongside cooling as cooling air reduces the amount of moisture it is able to 'hold', resulting in condensation and so dehumidification. 'Close' humidity control (to within 10%) can involve cooling and dehumidification, then re-heating and re-humidification.
- NB CIBSE Guide B defines refrigeration as 'the process of removing heat' and heat rejection as 'the discharge of heat to waste or atmosphere or to a system permitting reclaim or recovery'.
Very broadly, HVAC systems can be centralised in a building, or local to the space they are serving, or a combination of both (for example local air handling units supplied by centrally-generated cooling). They may also be connected to a wider district heating or cooling network.
They may be integrated, with heating, ventilation and air conditioning provided by a single system, for example, air handling units connected to ductwork, or they may be a combination of separate systems, for example mechanical ventilation but with radiators for heating and local comfort cooling units.
They may also include passive or 'natural' systems such as natural ventilation.
In mechanically ventilated commercial developments HVAC is often provided by air handling units connected to ductwork that supplies air to and extracts air from internal spaces. Air handling units typically comprise an insulated box that might include some, or all of the following components; filter racks or chambers, a fan (or blower), heating elements, cooling elements, dehumidification, sound attenuators and dampers. Air handling units that consist of only a fan and a heating or cooling element, located within the space they are serving, may be referred to as fan coil units (FCU). See Air handling units for more information.
HVAC can consume large amounts of energy, and where possible, demand should be reduced and passive systems adopted.
Extracting internal air and replacing it with outside air can increase the need for heating and cooling. This can be reduced by re-circulating a proportion of internal air, or by heat recovery ventilation (HRV) that recovers heat from extract air and to pre-heat incoming fresh air.
It is important that HVAC systems are considered together during the design process, even where they consist of independent systems. This is because of the interaction between heating, cooling, humidity control and ventilation. This is particularly complicated when other elements of environmental behaviour are considered such as solar gain, natural ventilation, thermal mass and so on.
The design of HVAC systems is generally a specialist task, undertaken by a building services engineer, and because of its interaction with other elements of the building it is important that it is considered from the outset, as a fundamental part of the design process, and not an 'add on' at the end.
 Related articles on Designing Buildings Wiki
- Air conditioning.
- Air conditioning inspection.
- Air handling unit.
- Building energy management systems (BEMS) for data centres.
- Building engineering physics.
- Building management systems.
- Building services
- Building services engineer
- Chilled beam.
- Chiller unit.
- Chilled water.
- Cooling systems for buildings.
- Cooling tower design and construction.
- Constant air volume.
- Dew point.
- Displacement ventilation.
- District energy.
- Electrical control systems.
- Evaporative cooling.
- Fan coil unit.
- Heat recovery.
- Mechanical, electrical and plumbing MEP.
- Mechanical ventilation.
- Natural ventilation.
- Radiant heating.
- Retrofit, refurbishment and the growth of connected HVAC technology.
- Thermal comfort.
- Variable air volume VAV.
- Variable refrigerant flow.
 External references
Featured articles and news
We attended Peter Barber's keynote lecture discussing the role of the street in shaping the public life of the city.
What are the main changes and new provisions in the soon-to-be-published NEC4 supply contracts?
"It can feel like we’re never going to keep everybody happy". We spoke with CEO Sarah Beale about the tough challenges ahead for CITB.
Do you know your mono pitch from your purlin roof? Have a look at the different types of domestic roofs.
"The UK is lagging way behind China, India and the South Pacific" - Designing Buildings Wiki attended a discussion on smart cities.
BSRIA publish updated guide to mechanical building services systems.
Apple's new HQ opened to employees this week, and has been touted as 'the best office building in the world'.
The risk of moisture in hard-to-treat buildings.
Find out about the intricate art of pyrography.
Have a look at this newly-opened linear park on an elevated highway in Seoul.
The charity for the blind wants to encourage greater collaboration with built environment planners.
Read our review of a new book examining methods used to observe how sustainable buildings work in occupation.