- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 01 Sep 2020
Heating ventilation and air conditioning HVAC
Internal air quality can be maintained by a combination of introducing 'fresh' air into the building, extracting 'stale air' and by filtration. Ventilation may be natural, mechanical, or mixed mode (a hybrid system). See Ventilation for more information.
Internal temperatures can be regulated by heating and cooling. Typically, this is achieved by heated water (or sometimes steam) and chilled water that is generated by boilers and chillers and then used in heating coils and cooling coils as part of the ventilation system. Alternatively, hot water may be used to supply systems such as radiators, underfloor heating and so on.
Humidity can be regulated by ventilation, dehumidification and humidification. Dehumidification is often provided alongside cooling as cooling air reduces the amount of moisture air is able to 'hold', resulting in condensation. 'Close' humidity control (to within 10%) can involve cooling and dehumidification, then re-heating and re-humidification.
Very broadly, HVAC systems can be centralised in a building, or local to the space they are serving, or a combination of both (for example, local air handling units supplied by centrally-generated cooling). They may also be connected to a wider district heating or cooling network.
They may be integrated, with heating, ventilation and air conditioning provided by a single system, for example, air handling units connected to ductwork, or they may be a combination of separate systems, for example mechanical ventilation with radiators for heating and local comfort cooling units.
In mechanically ventilated commercial developments, HVAC is often provided by air handling units (AHU) connected to ductwork that supplies air to and extracts air from internal spaces. Air handling units typically comprise an insulated box that might include some, or all of the following components; filter racks or chambers, a fan (or blower), heating elements, cooling elements, dehumidification, sound attenuators and dampers. Air handling units that consist of only a fan and a heating or cooling element, located within the space they are serving, may be referred to as fan coil units (FCU). See Air handling units for more information.
Extracting internal air and replacing it with outside air can increase the need for heating and cooling. This can be reduced by re-circulating a proportion of internal air, or by heat recovery ventilation (HRV) that recovers heat from extract air and uses it to pre-heat incoming fresh air.
It is important that all aspects of HVAC systems are considered together during the design process, even where involve independent systems. This is because of the interaction between heating, cooling, humidity control and ventilation. This is particularly complicated when other elements of environmental behaviour are considered such as solar gain, natural ventilation, thermal mass, and so on.
The design of HVAC systems is generally a specialist task, undertaken by a building services engineer, and because of its interaction with other elements of the building it is important that it is considered from the outset, as a fundamental part of the design process, and not an 'add on' at the end.
 Related articles on Designing Buildings Wiki
- Africa tops world AC growth forecasts.
- Air conditioning.
- Air conditioning inspection.
- Air handling unit.
- Building energy management systems (BEMS) for data centres.
- Building engineering physics.
- Building management systems.
- Building services
- Building services engineer
- Chilled beam.
- Chiller unit.
- Chilled water.
- Cooling systems for buildings.
- Constant air volume.
- Displacement ventilation.
- Drivers of change in global heating markets.
- Electrical control systems.
- Evaporative cooling.
- Fan coil unit.
- Heat recovery.
- HVAC balancing.
- Mechanical, electrical and plumbing MEP.
- Mechanical ventilation.
- Natural ventilation.
- Plant room.
- Radiant heating.
- Retrofit, refurbishment and the growth of connected HVAC technology.
- Smart connected HVAC market.
- Tempering heating.
- Thermal comfort.
- Variable air volume VAV.
- Variable refrigerant flow.
 External references
Featured articles and news
Results show guarded optimism and payment concerns.
Noteworthy navigable aqueducts.
Technology is making remote work a reality.
Carefully placed structures add drama to pastoral vistas.
Report provides actions required by 2030 to achieve a zero carbon economy.
What type of cool roof is most suitable?
Active Travel programme prioritises cyclists and pedestrians.
CIAT issues caution for use of new standard.
Industry leaders discuss climate change, the economy and other influences.
The building manager is key to operations.
The impact Scotland’s dynamic coast has on the historic environment.
IHBC announces role in new APPG.