- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 10 Jan 2018
- Flame cutting.
- Grinding and drilling (when flammable materials are present).
- Use of any equipment that incorporates a flame.
Hot works can pose a significant fire risk, from both the initial risks of ignition and as a cause of rapid fire spread. According to BS 9999, only if no satisfactory alternative method is feasible should hot work be undertaken.
Precautions should include:
- Carrying out the hot work outdoors or in specially-designated areas that minimise fire risk if possible.
- Scheduling hot works during periods when other works are quieter.
- Applying safe systems for undertaking the hot works.
 Hot work permit
BS 9999 recommends that a ‘hot work permit’ be followed in order to ensure actions are taken to mitigate and minimise risks before, during and after the works. The permit is appropriate when there are flammable materials in close proximity to the works, and when the work environment is not ordinarily used for such activities.
The permit is used:
- To ensure there is a formal check confirming appropriate work processes are being adhered to.
- To provide time limits for safe working.
- To provide for special PPE (personal protective equipment) or communication methods.
- For coordinating work activities.
- To ensure proper supervision throughout.
When being employed to complete hot works contractors may be required to use the client’s hot work procedure, or they may use a suitable procedure of their own. In the case of the latter, the client must ensure that the contractor is using a suitable hot work procedure.
There are varying levels of risk depending on the type of work and the area within the building that it is taking place. As a result, the hot work permit system should be adapted to the particular needs and risks. In terms of the proposed works, the permit should be designed to provide as much information as possible.
Typically, the hot work permit will identify:
- Administrative details (permit title, number, job location, etc.).
- Description of the work to be undertaken.
- The person/s carrying out the work.
- Likely length of time to complete the work.
- Identified hazards and required precautions.
- Work methods that are required.
- Types of fire-fighting equipment available.
- Combustible materials removed before work commences.
- Floors swept clean and combustible surfaces covered with heat protections mats.
- Walls covered and combustibles moved away.
- Elimination of explosive atmosphere in the area.
- Removal of flammable liquids and gas cylinders.
- Appropriate screening, protection and display of safety notices.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
An architectural technologist in Germany.
3 World Trade Center designed by RSH+P
The struggle to achieve net-zero emissions by 2050.
What is 'agent of change' and who does it protect?
A consistent and measurable approach to home adaptation.
Acknowledging and challenging the realms and interpretations of heritage.
Embodied carbon in construction steel.
A prototype for assessing circularity in buildings.
New Wiki site is set to make BIM mainstream.
FMEA is a step-by-step approach for collecting knowledge about possible points of failure.
The various types and everything else.