- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 14 Nov 2014
Constant air volume CAV
- Moderate internal temperatures.
- Replenish oxygen.
- Reduce the accumulation of moisture, odours, bacteria, dust, carbon dioxide, smoke and other contaminants that can build up during occupied periods.
- Create air movement, which improves the comfort of occupants.
Very broadly, ventilation in buildings can be classified as ‘natural’ or ‘mechanical’. Mechanical ventilation systems can also include heating, cooling, humidity control and air filtration. These functions are often described collectively as HVAC (Heating Ventilation and Air Conditioning).
- Variable air volume (VAV), in which the temperature of the supply air remains constant, but the volume varies (also known as variable volume, constant temperature VV-CT).
- Constant air volume (CAV) in which the volume of air supply remains constant, but the temperature varies (also known as constant volume, variable temperature CV-VT, or constant volume CV).
- Variable volume, variable temperature (VV-VT sometimes referred to as variable volume and temperature - VVT).
Constant air volume (CAV) systems are becoming less common in new buildings as VAV systems tend to provide closer control of air temperature and require lower fan speeds, as a result of which they can use less energy and generate less noise. However, CAV systems are still used in small and medium-sized premises with straight-forward HVAC requirements, as they can be relatively simple to install, can have a lower capital cost and tend to be reliable.
They are particularly common in simple systems where fan coil units are supplied with a constant volume of ‘fresh’ air.
This system can be enhanced by reheating the supply air in CAV terminal units to provide additional local control. This might be appropriate where there are some minor local variations to thermal demand. In this case, air is supplied to the system at the lowest temperature required and then its temperature is increased as necessary locally.
Alternatively, 'mixed-air' or 'dual-duct' systems can provide both heated and cooled air, the proportions of which are regulated locally in mixing boxes. This might be appropriate where there are significant differences in thermal demand. Air is supplied at the lowest and highest temperatures required and then mixed locally as necessary.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
How to ensure UK transport infrastructure copes with severe winter weather.
Location shortlist for controversial new footbridge revealed.
Under the Party Wall Act a property owner has the legal right to do works that might otherwise constitute trespass or nuisance.
BSRIA examine the 'unpredictable' 2018 global air conditioning market.
ICE publish new report calling for new sector-wide body to help avert structural failures.
The rainbow JCB will be making a welcome return to the London Build Expo on 23 and 24 October at Olympia.
An introductory article to external works - all activities carried out to the external environment of a building project.
With the clock ticking, RIBA say that a 'no deal Brexit' will be "disastrous" for the architecture profession.
The focus is generally on the lime binder, but the aggregate is actually the most significant element.
The importance of communication, collaboration and simplicity when planning construction projects.