- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Jul 2019
Developing test methods to assess video flame and video smoke detectors
Video fire detectors emerged as a new means of fire detection around 2004, particularly in large indoor spaces such as those in atria, warehouses and industrial complexes. Detection of fires in such spaces has traditionally been provided by optical-beam smoke and aspirating smoke detectors, or flame detectors – but video fire detectors potentially offer important advantages.
A video detector is alerted to the presence of a fire by identifying the characteristic signatures of smoke or flame within the field of view of its camera. The images from the live video feed are analysed by sophisticated algorithms to detect these signatures. There are two detector types – video flame detectors (VFDs) that recognise flaming fires, and video smoke detectors (VSDs) that are alerted to the presence of moving smoke. Some systems can have both sets of algorithms working independently at the same time.
The detector does not need to be in proximity to smoke or flames to detect fire as (provided there is direct line of sight) it can ‘see’ them. This enables a quicker response than is generally achievable by conventional smoke and flame detectors, and can also provide a visual verification of fire.
 No current means of testing/assessing capabilities
While there has been a significant amount of fundamental research work on the capabilities and potential applications of video fire detectors, due to their complexity there are currently no defined and robust methods of assessing the capabilities of these detectors for testing and certification purposes.
Work by BRE Global and the Fire Industry Association (FIA) to develop test methodologies for these technologies has identified the greatest obstacle to be a lack of benchmark tests of basic performance. These are needed to perform the fundamental tests of repeatability, reproducibility and environmental testing defined in the EN 54 Fire detection and fire alarm systems standard. Additionally, operational performance tests are needed to verify the absolute capabilities of video detectors in detecting the fires anticipated in service environments.
A BRE Trust-supported research programme was established by BRE, in collaboration with video fire detector manufacturers, to develop benchmark and operational performance test methods for both video flame and video smoke detectors. To gain the necessary underpinning knowledge on the performance capabilities of video fire detectors, the research group has developed methods for bench testing and full-scale fire testing of these systems.
The group’s development of methodologies for assessing the performance of VFDs and VSDs has been summarised in a briefing paper that can be freely downloaded from here. It is now expected that these methodologies will support the development of a test standard and associated code of practice.
 About this article
 Related articles on Designing Buildings Wiki
- BS 5839-1.
- Carbon monoxide.
- Carbon monoxide detector.
- Domestic smoke alarms DG525.
- Fire detection and alarm system.
- Fire detector.
- Heat alarm.
- Ionisation smoke alarm.
- Multi-sensor alarm.
- Optical smoke alarm.
- Smoke detection in high ceiling spaces.
- The causes of false fire alarms in buildings.
Featured articles and news
A lighthouse history from Eddystone to Fastnet. Book review.
Telling the story of the Government Code and Cipher School.
Are you an experienced writer with a practical understanding of the industry?
Hagia Sophia, Istanbul.
New Dwelling House at Grange View.
The causes of sinkholes.
The growth of megacities.
The restoration of Big Ben
Improving fire-safety design with computer modelling.
Sound insulation testing.
Making commercial property more efficient.
SF6 is at the heart of the electrical industry.
Caring for graves and memorials at 23,000 locations.
A return to historical forms and local identities. Book review.
Black water recycling.