- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 10 May 2021
What to know about foundation earthing
The concept of foundation earthing – installing earth electrodes as a closed ring in the foundations of buildings – is by now familiar. What foundation earthing means in practical terms is perhaps less well understood.
 Establishing a mandate
When the Draft for Public Comment (DPC) for the 18th Edition Wiring Regulations (BS 7671: 2018) was opened in 2017, a mandate for foundation earthing was proposed, though this never made it into the final edition.
It is worth clarifying at this point that proposals in the DPC are liable to change. There is no guarantee any proposal will be included in the final draft. Foundation earthing is nevertheless an important concept, and we will nod to the wording used in the DPC.
 DPC clarifications
The DPC states in Regulation [IP address hidden] that (and I paraphrase) for new installations constructed upon foundations, some form of additional earthing will be required. Three options are proposed:
- Concrete-embedded foundation earth electrode.
- Soil-embedded ring earth electrode.
- Equivalent electrode using metalwork of a steel framed building.
Essentially, the idea is to connect the earthing system of a building to an additional earth, using foundation rebar or a ring electrode in the soil. This can prevent significant voltage increases in event of a fault.
 Harmonising foundation earthing approaches
Proper foundation earthing involves a certain amount of coordination between the electrical contractor and those involved in the construction of the foundations, to ensure that components work in harmony.
If you ever come to discuss foundation earthing with German or French peers, you may find them incredibly well-versed on the subject. Unlike current British Standards, European Standards for foundation earthing are many and detailed, right down to recommended types of soil, concrete and connections.
But for now, in the UK, foundation earthing is not essential, though you may come across it. BS 7430, the code of practice for protective earthing of electrical installations, gives information on foundation earthing should an electrical designer or installer wish to find out more.
Future editions of the wiring regulations may well require designers and contractors to implement more foundation earthing systems, though this will not be clear until Amendment 2 is released in 2022.
This article originally appeared on the ECA website. It was written by Gary Parker, ECA Technical Manager and published on 4 May 2021.
 Related articles on Designing Buildings Wiki
- 18th Edition Wiring Regulations.
- Articles by the Electrical Contractors' Association (ECA).
- Comparison of SMM7 with NRM2.
- Electrical wiring.
- Energy related products regulations.
- Radial circuit.
Featured articles and news
Saint Michael’s Kirkyard - a Presbyterian Valhalla. Book review.
Facing the impact of the COVID and the internet.
Preparing for the return of employees.
Using rainscreen walls to address energy efficiency.
Integrity of fire product marketing - post-Grenfell - addressed.
Data measurement and carbon reduction efforts.
Actuate UK issues stark warning.
Department for Levelling Up, Housing and Communities replaces MHCLG.
Protecting heritage from disasters. Book review.
Three structures forever changed people's lives for the better.
ECA comments on findings of BEIS Green Jobs Task Force.