- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 18 Jul 2017
Safe ductwork - Loss Prevention Standard (LPS 2084)
The Regulatory Reform (Fire Safety) Order 2005 requires that a building’s owner or workplace manager nominates a responsible person to identify all possible sources of fire and eliminate, or at least minimise the risk, to the building’s occupants.
Regular kitchen extraction cleaning will remove one of the most common causes of fire within the kitchen and is imperative to ensure the safety of the building and its occupants and reduce the risk of a fire caused by grease build-up in the extraction system.
Regardless of the efficiency of canopy filters, it is inevitable that grease deposits will build up over time in kitchen extraction ductwork and canopies. If left, grease will become baked on and carbonised making it extremely difficult to remove, thus reducing the effectiveness of the extraction system, potentially shortening the life of the fan and creating a serious fire hazard that may propagate around the building.
The Loss Prevention Standard (LPS 2084), published in May 2017 by BRE Global, seeks to minimise fire risk from ducting. It was prepared in response to issues caused by ineffective cleaning and maintenance and defines the Loss Prevention Certification Board (LPCB) requirements for the approval of companies carrying out inspection, cleaning and maintenance of ductwork systems that may be contaminated with combustible deposits.
Certified companies with LPS 2084 have to:
- Meet the requirements of the client contract.
- Document and report correctly.
- Identify and record areas of limited access where inspection, cleaning and maintenance are impractical and communicate these limitations to the client.
- Provide recommendations for access improvements to better facilitate the ongoing cleaning and maintenance of the ductwork system.
LPS 2084 is of great importance in an industry with little regulation.
Certified companies will be audited by BRE Global on a regular basis to ensure they continue to adhere to the requirements of the standard. Auditors will check records and supporting documentation covering the contract itself, storage and handling of cleaning materials, disposal, training and so on.
Specifying LPCB approved products and services enables the responsible person to reduce risk by showing due-diligence in the selection of products and services that can be trusted to perform as specified.
This article was originally published here on 17 July 2017 by BRE Group.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
When is there a right to light, and what happens if it is obstructed?
What would the nationalisation of economic infrastructure mean for GB?
A new guide to improving value by reducing design error.
We've reached 80,000 page views a day and 10,000 registered users. Why not join them?
A masterplan is a framework within which a location is encouraged to develop or change. Read our introductory article.
New consultation announced on a specialist Housing Court to settle landlord-tenant disputes.
ICE responds to a transport consultation advising the government to make decisions enabling more inclusive cities.
BRE and Loughborough University complete first phase refurbishment of demonstration home.
How the risk of collapse of fibrous plaster ceilings is being addressed in theatres.
If you’re a great writer and have practical experience of the construction industry, it could be you.
Frustrated by long documents or technical jargon? Put off by sign-up forms or costs? Take this 5 min survey to help improve construction knowledge.