Absorption refrigeration in buildings
Refrigerants are used in buildings:
- For heating, ventilation and air conditioning (HVAC) systems.
- To provide cooling for refrigeration.
- To provide cooling for industrial processes.
Absorption and compression refrigeration both work on a similar basis, in that a refrigerant boils at a low temperature and pressure, and is then is then pressurised, and condensed at a higher temperature and pressure. The process of condensing releases heat which is rejected.
In ‘conventional’ compression systems, a liquid refrigerant with a low boiling point absorbs heat from the body that is being cooled and boils in an evaporator to form a gas. The resulting gas is then compressed, which increases its temperature further. The gas is then condensed, releasing its latent heat which is rejected. The process then repeats.
However, whilst in compression refrigeration, the compression and refrigerant flow is achieved by an electrical compressor, in absorption refrigeration, compression is achieved by heating, and circulation is achieved absorbing the refrigerant into and absorber and by an electrical pump. This pump uses much less energy than a compressor.
The liquid refrigerant absorbs heat from the body that is to be cooled (in buildings this may be water that once cool is circulated back to the building) and the refrigerant evaporates at low pressure (in the ‘evaporator’). It is then absorbed into an absorber fluid and the refrigerant / absorber mixture is heated (in the ‘generator’). The refrigerant evaporates again, this time at higher temperature and pressure. The refrigerant is then condensed (in the ‘condenser’) and the heat rejected. The process is then repeated.
The heat in absorption refrigeration can be gas powered, but absorption refrigeration is particularly suited to situations where ‘waste’, or other low-cost heat supply is available, such as; surplus heat from combined heat and power plant (CHP), heat from industrial processes, district heating, geothermal or solar thermal energy and so on.
Absorption refrigeration was first developed in France in 1850’s, but it was not commercially exploited until the 1920’s.
The most common combinations of refrigerant and absorbent fluid are:
Ammonia is not an ozone depleting gas or a global warming gas. However it is flammable and toxic so additional precautions are necessary in design and use.
 Related articles on Designing Buildings Wiki
- Absorption heat pump.
- Air conditioning.
- Air handling unit.
- Chilled beam.
- Chiller unit.
- Chilled water.
- Compression refrigeration.
- Constant air volume.
- Evaporative cooling.
- Fan coil unit.
- Heat pumps
- Passive building design.
- Thermal comfort.
- Variable air volume.
- Variable refrigerant flow.
 External references
Featured articles and news
Summary of a new ICE Transport journal which says improving transport infrastructure is essential to eradicating global poverty.
BRE look at a new government report into the accuracy of heat meter testing.
Herzog & de Meuron get planning permission for revamp of Chelsea FC football stadium.
UK-GBC green paper proposes more powers for cities on new-build housing.
The Pompidou Centre – not a monument but an event.
The Chartered Institute of Building restructures and launches 29 new local hubs.
Designing Buildings Wiki talks to the founder of the world's first indoor biophilic gym, now open in London.
£1.3bn Swansea Bay project to be backed as a 'pathfinder' for other tidal lagoon projects.
Designs released for a proposed Las Vegas stadium to entice the Oakland Raiders.
Have a look at these award-winning concept designs for a thermal bath in Latvia.
Flagship project no longer "a going concern" according to the Garden Bridge Trust as funding slows.
How the work of 20th century urbanist Jane Jacobs continues to resonate in light of the government's garden village plans.