- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 15 Nov 2021
The Illustrated Guide to Renewable Technologies BG 1/2008, By Kevin Pennycook, published by BSRIA in March 2008, states: ‘Adsorption chillers, like absorption chillers, are driven by an external heat source; however they have the advantage that the required input temperature is between 60oC and 95oC. This means that relatively low cost flat-plate solar collectors can be used to provide the heat source to drive the refrigerant process. An adsorption chiller consists of a pressure vessel divided into four chambers. These are the evaporator (lower chamber), the generator/receiver (second and third chambers) and the condenser (top chamber). The generator and receiver are linked by valves which automatically open depending on the pressure differences within the chiller. Adsorption chillers use water as the cooling medium and silica gel as the adsorbent. At low pressures, water vapourises at low temperatures. Silica gel can bond large amounts of water without loss, reversibly (and without increasing in volume), releasing the water again when heat is applied.’
Featured articles and news
Meaning, understanding and implementation.
Kick-start attempts causes 50% jump from December.
From climate to cost to cold bridges and design flexibility.
In a changing world at the APM PM SIG conference.
The glass product that opened up new possibilities.
Campaigning for buildings of all periods.
Full life cycle assessments, impact categories and more.
Lansink's ladder to resin identification codes. Less is more.
Basic components in an increasingly complex material world.
Get to know the new requirements and the new terms.
Reporting on Payment Practices and Performance Regs.
Welcomed with a skills shortage warning.
The ultimate companion for building services excellence.
CIOB joins leading organisations to warn leaders.