- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 21 Oct 2020
An automatic sprinkler system consists of a water supply (tank, pump and valves) and sprinkler installation (pipes and heads). Almost all buildings over 30m high must be fitted with a sprinkler system installed in accordance with the appropriate British Standards.
The specification of the design depends primarily on the hazard classification of the occupancy of the building. The specifications include head spacing dimensions, assumed area of maximum operation (number of heads in-operation), design density (water discharge), water supply period and tank volume.
The system’s heat sensitive element can be constructed from soldered links or glass bulbs containing various liquids. Some sprinkler head ampules contain a mixture of alcohol and water or glycerin and water. When hot air reaches the ceiling, this liquid expands, causing the container to break and activate the sprinkler head so it can distribute water and extinguish the fire.
Sprinkler heads normally activate at 68°C. Each sprinkler head acts as its own heat detector and only those in the area of the fire will be activated. An individual sprinkler head typically covers 9m².
The flow of water from the sprinkler head is generally distributed by a flower-shaped deflector device directly below the sprinkler. This shape is designed to control the flow of the water so it is evenly distributed.
 Sprinkler head variations
There are quick response (QR) fire sprinkler heads which have a smaller ampule so they can activate in a shorter period of time. These devices typically distribute water across the ceiling or down walls as a method of controlling fire by preventing it from rising.
There are several different sprinkler head orientation options. The most common are:
- Pendant heads use a convex deflector to distribute water in a domed or conical pattern.
- Upright heads spray water upwards to a concave deflector, producing a dome-shaped spray pattern.
- Sidewall heads have a semicircular deflector that produces a crescent-shaped spray pattern.
- Concealed heads are pendant or sidewall sprinkler heads that have been covered with a fire sprinkler cover plate. This cover lowers when a certain temperature has been reached. The fire sprinkler head is then revealed so it is able to activate.
 Related articles on Designing Buildings Wiki
Featured articles and news
The last few days, but action needed over the next decade.
80 construction leaders and companies from across the UK.
Promoting the importance of building and fire safety.
A brief run through essential training tips from a user.
A comprehensive guide from a Cohesive BIM wiki user.
From the basics to the future from our Cohesive BIM wiki.
As electrical sector feels skills shortage bite.
CIOB Academy’s course take-up inked to external factors.
Q and A with self-representing artist, Hannah Shergold.
And publishes three-year strategic plan.
Introducing changes to make it more effective from 2024.
Shortlist announced for 2023 public choice award vote.
The last of the Victorians. Book review.
An exotic name that is shrouded in mystery.
From practice to research and the business of materials.