- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 07 Feb 2018
Existing guidance on fire compartmentation in roof voids
This article originally appeared as part of Fire in the hole. Designing out fire risk in roof voids in the Spring 2016 edition of AT Magazine, published by the Chartered Institute of Architectural Technologists (CIAT).
Guidance is presented in Section 8 of Approved Document B  on the means of satisfying the compartmentation requirement at the junction of a compartment wall with the roof. The guidance essentially involves:
- Fire stopping up to the underside of the roof covering or deck and restricting flame spread in the area around the junction, or
- Continuing the compartment wall up through the roof extending beyond the top surface of the roof covering.
Further guidance is available from the NHBC  to resist fire spread at the junction between roofs and compartment or separating walls. The NHBC guidance requires the junction to be fire stopped to prevent fire, smoke and fire spread from one compartment to the next across the wall. Although specialist information on fire stopping is available through the Association for Specialist Fire Protection (ASFP) , the particular detailing of compartmentation within the roof spaces of residential buildings is often left to non-specialist construction staff. Standard details, such as spandrel panels used in timber frame construction, provide a simple means of achieving the required level of fire resistance but do not account for fire stopping around any eaves cavity or the difficulties of providing fire stopping to the underside of the roof covering.
The current guidance in Approved Document B is the main source of information for those involved in specifying and providing compartmentation within roof voids. The particular issue of the detail at the junction between a separating wall and the roof in relation to preventing fire spread between dwellings was covered by the BRE Housing Defects Prevention Unit in Defect Action Sheets 7  and 8 . Further information was provided on cavity barriers and fire stops including cavities within roof spaces, in BRE Digests 214  and 215 . Full texts of the regulations can be found at www.planningportal.co.uk
-  HM Government. The Building Regulations 2010. Fire safety. Approved Document B Volume 2 – Buildings other than dwellinghouses. London. DCLG, 2006 edition incorporating 2007, 2010 and 2013 amendments, Crown Copyright 2006.
-  NHBC Design Standards Part 7 Roofs – Chapter 7.2 Pitched roofs, NHBC, Milton Keynes, Effective from 1 January 2012.
-  Association for Specialist Fire Protection (ASFP), Ensuring Best Practice for passive fire protection in buildings, Published by BRE Watford.
-  Building Research Establishment, BRE Housing Defects Prevention Unit, Defect Action Sheet (Design) 7, Pitched roofs: boxed eaves – preventing fire spread between dwellings, Crown Copyright 1982.
-  Building Research Establishment, BRE Housing Defects Prevention Unit, Defect Action Sheet (Design) 8, Pitched roofs: separating wall/roof junction - preventing fire spread between dwellings, Crown Copyright 1982.
-  Building Research Establishment Digest 214, Cavity barriers and fire stops: Part 1, Department of the Environment, HMSO, June 1978.
-  Building Research Establishment Digest 215, Cavity barriers and fire stops: Part 2, Department of the Environment, HMSO, July 1978.
See also: Designing out fire risk in roof voids.
Featured articles and news
The built environment can unlock opportunities for skills.
Additionality is a concept applied to activities and projects.
Some HPL cladding is very unlikely to adequately resist the spread of fire.
What a chartered architectural technologist does.
Building design and construction fees.
The world heritage list has evolved to embrace built, cultural and natural heritage.
The Ocean Cleanup project
The various types of bond and when they are used.
It's vital the industry responds to proposals for reform of the safety regulatory system.
RSHP's Merano wins RIBA accolade.
How to differentiate between partial possession and early use.
Ofwat proposes £12 billion additional investment and £50 bill reductions.