- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 31 Aug 2017
A wellpoint, also known as a drive point, is a small diameter well used for dewatering. It consists of a shallow shaft, a dewatering pump to draw water, a riser pipe which connects the wellpoint to the surface, and a small ‘well’ that fills up.
The riser pipes tend to be around 38-50 mm in diameter, with slots or openings at the bottom which enable water to be drawn up using the pump. The size of the openings is determined by the relative grain size of the water-bearing formation material. The openings should be large enough to allow water to enter the tube, but small enough to keep the water-bearing formation in place.
The riser pipe is often connected to a common header main pipe through a flexbow. This flexbow incorporates an adjustable valve which serves two purposes: firstly, it controls the flow of air and water entering the system; and secondly, allows a clear view of what is being pumped. The header main pipe is then connected to a wellpoint dewatering pump.
Wellpoints are fairly versatile and can be used for a wide range of applications. They are suitable for shallow foundations and trench works, particularly for long pipeline trenches where wellpoints may be installed in parallel by special trenching machines.
They can also be used for the irrigation of small to medium-sized residential gardens. If the water yield from one well is not sufficient for running an irrigation system, a second can be installed and connected to the first, enabling them to operate as one system.
They can also be used around the perimeter of excavations as an alternative to boreholes, as a means of lowering and controlling groundwater levels. They can be more cost- and time-efficient than a borehole due to the shallower depths required. In appropriate ground conditions, a wellpoint system can be installed very quickly. Traditional drilling techniques, such as jetting or auguring are typically used for installation.
Wellpoints tend not to yield large quantities of water – around 5 gallons per minute is typical. There is generally a limit of about 5-6 m in height over which water can be drawn as the vacuum is limited in practice to 0 bar. However, a second stage of wellpoints can be installed at a lower level if greater depths are required. They are capable of dealing with very low flows in silty sands as well as much larger flows in coarse sands and gravel.
Some of the benefits of using wellpoints include:
- Quick installation in most ground conditions.
- Easy to maintain.
- Capable of being used for both large and small-scale projects.
- Self-jetting wellpoints can be used in situations where there is limited space.
 Related articles on Designing Buildings Wiki
Featured articles and news
Timber is a natural carbon sink, but it must not end up in landfill at the end of its useful life.
BSRIA has collaborated with the Department of Health on research into air permeability in isolation rooms.
New step-by-step route maps for implementing effective surface water management measures are published.
GMP is an agreement with a contractor that the contract sum will not exceed a specified maximum. Read more here.
The BREEAM Sustainability Champion is changing to the Advisory Professional - here's what you need to know.
A fresh round of job-cuts takes the total number of redundancies to over 1,000.
Read our introductory article to the completion date in construction contracts.
Almost 90% of freight in London is moved by road. The River Thames could add much needed extra capacity.
National Infrastructure Commission warn that large infrastructure projects are at risk of falling behind.
The quality of Cambridge owes as much to its open spaces as to its architectural uniqueness.