- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 24 Jul 2017
Uninterrupted power supply for buildings
To help develop this article, click ‘Edit this article’ above.
An uninterrupted power supply (UPS), sometimes referred to as an uninterruptible, or uninterruptable power supply, provides an alternative ‘no-break’ electrical supply that can be required in situations where it is important there is no loss of electrical supply, even if the primary supply fails.
- Emergency services and medical facilities.
- Leisure and sports venues where scheduled and ticketed events take place.
- Data centres.
- Financial services.
- Some industrial processes.
It might also be necessary to support specific critical services, such as:
- Information and communications technology (ICT).
- Emergency lighting.
- Fire alarms and other safety systems.
UPS can be also be useful when the primary power source is shut down intentionally, for example during maintenance, and some systems can correct power supply issues such as voltage spikes.
A UPS is not the same as an auxiliary, standby or emergency power supply as it provides virtually instantaneous supply, avoiding any power interruption.
Generally this will include the use of batteries, supercapacitors, or flywheels (rotary UPS) that either allow equipment to be powered down safely when the mains supply is interrupted, or provide power for long enough for an auxiliary supply to come online. This may only take a few minutes.
Auxiliary power might be provided by:
- Simple packaged battery units that can be incorporated into equipment such as comms cabinets.
- Stand-alone battery units.
- Standby generators.
They might be very small units that supply a single computer, to large installations that supply a major industrial process.
UPS systems will generally include some form of automatic mains failure detection (AMF) and an automated changeover process. They may also detect power restoration and automatically revert to the mains supply.
If continued power supply is critical, the UPS may be provided by a number of smaller packaged units, rather than by a single source, which might introduce a potential source of failure itself. The packaged units might include some ‘redundancy’ so that if one or more of the units fail, there is still adequate supply.
UPS require careful design, particularly where they are supplying critical systems. Regular maintenance is necessary to ensure continued performance.
 Related articles on Designing Buildings Wiki
Featured articles and news
Rogers Stirk Harbour + Partners' release new images of soon-to-open 3WTC tower in New York.
A document can be called a bond or a guarantee. Does the name matter and what is the difference between them?
New briefing note is launched focusing on increasing knowledge of housing that promotes health and wellbeing.
Arbitration is a private, contractual form of dispute resolution used in the construction industry.
The European Parliament has approved a revised Energy Performance of Buildings directive.
One in six MPs supports the ring-fencing of retentions as proposed in the 'Aldous Bill'.
A stakeholder is anyone who has an interest in the process or outcome of a construction project.
BRE launches online self-assessment tool for ethical labour sourcing.
Tower refurbishment failed to meet safety standards on several counts, according to leaked report.
It may seem obvious but what does the term 'structure' refer to within a built environment context?
Carillion's liabilities could be much higher than previously thought, according to Receiver.