Uninterrupted power supply for buildings
To help develop this article, click ‘Edit this article’ above.
An uninterrupted power supply (UPS), sometimes referred to as an uninterruptible, or uninterruptable power supply, provides an alternative ‘no-break’ electrical supply that can be required in situations where it is important there is no loss of electrical supply, even if the primary supply fails.
Typically this is necessary where a loss of power could result in a risk to health or disruption to business, for example:
- Emergency services and medical facilities.
- Leisure and sports venues where scheduled and ticketed events take place.
- Data centres.
- Financial services.
- Some industrial processes.
It might also be necessary to support specific critical services, such as:
- Information and communications technology (ICT).
- Emergency lighting.
- Fire alarms and other safety systems.
UPS can be also be useful when the primary power source is shut down intentionally, for example during maintenance, and some systems can correct power supply issues such as voltage spikes.
A UPS is not the same as an auxiliary, standby or emergency power supply as it provides virtually instantaneous supply, avoiding any power interruption.
Generally this will include the use of batteries, supercapacitors, or flywheels (rotary UPS) that either allow equipment to be powered down safely when the mains supply is interrupted, or provide power for long enough for an auxiliary supply to come online. This may only take a few minutes.
Auxiliary power might be provided by:
- Simple packaged battery units that can be incorporated into equipment such as comms cabinets.
- Stand-alone battery units.
- Standby generators.
They might be very small units that supply a single computer, to large installations that supply a major industrial process.
UPS systems will generally include some form of automatic mains failure detection (AMF) and an automated changeover process. They may also detect power restoration and automatically revert to the mains supply.
If continued power supply is critical, the UPS may be provided by a number of smaller packaged units, rather than by a single source, which might introduce a potential source of failure itself. The packaged units might include some ‘redundancy’ so that if one or more of the units fail, there is still adequate supply.
UPS require careful design, particularly where they are supplying critical systems. Regular maintenance is necessary to ensure continued performance.
 Related articles on Designing Buildings Wiki
Featured articles and news
UandI adds £1.5bn to development pipeline.
Here are 5 things leaders can do to create a truly circular economy.
Find out about the different types of delays on construction projects.
Researchers at Wien university have developed new system to create an inflatable concrete structure.
ICE responds to the first consultation on the government's industrial strategy post-Brexit.
Take a look at this newly-opened tower in Chicago with a remarkable 20:1 height-to-base ratio.
An Arc de Triomphe for the late-20th century, the La Grande Arche of Paris.
Richard Hayward of Legrand asks whether technology could help developers meet the needs of an increasingly diverse population.
Thomas Heatherwick's ambitious steel structure begins construction.
The principles, practice and formwork of one of the most important components of modern architecture.