- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 05 Jan 2021
|An electrical circuit that is protected against fire.|
Cabling should at least meet the requirements of PH 30 classification or an equivalent standard and should only pass through parts of the building in which fire risk is negligible.Protected circuits are required where it is critical that an electrical circuit continues to operate during a fire. This should include the use of sufficiently robust cables, careful selection of cable routes, and/or by the provision of physical protection in areas where cables may be susceptible to damage. Cable supports should generally be non-combustible and such that circuit integrity will not be reduced below that afforded by the cable.
Protected circuits should be separate from other circuits.
 Related articles on Designing Buildings Wiki
- Amendment 3 BS 7671 Requirements for Electrical Installations IET Wiring Regulations.
- Approved document B.
- Approved document P.
- Approved documents.
- Articles by the Electrical Contractors' Association (ECA).
- Building regulations.
- Consumer unit.
- Electrical appliance.
- Electrical control systems.
- Electrical drawing.
- Electrical engineer.
- Glossary of electrical terms.
 External references
- BS 5266-1.
- BS 5839-1.
- BS 7346-6.
- BS EN 50200:2006.
Featured articles and news
IHBC publishes response to consultation.
Institute applauds funding initiatives but presses for additional retrofit and tax measures.
The switch from analogue to digital has begun.
The fourth industrial revolution is well underway.
Free online resource will offer guidance on conserving places and the planet during COP26.
Government allocates additional money for building new homes on derelict land.
Smart built environments can be designed around the requirements of real people.
Consistency is at the core of realistic strategies.
Entries being accepted until 20 November 2021.