- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 05 Jun 2019
|An electrical circuit protected against fire.|
Protected circuits are required where it is critical that an electrical circuit continues to operate during a fire. This should include the use of sufficiently robust cables, careful selection of cable routes, and/or by the provision of physical protection in areas where cables may be susceptible to damage. Cable supports should generally be non-combustible and such that circuit integrity will not be reduced below that afforded by the cable.
Protected circuits should be separate from other circuits.
 Related articles on Designing Buildings Wiki
- Amendment 3 BS 7671 Requirements for Electrical Installations IET Wiring Regulations.
- Approved document B.
- Approved document P.
- Approved documents.
- Articles by the Electrical Contractors' Association (ECA).
- Building regulations.
- Consumer unit.
- Electrical appliance.
- Electrical control systems.
- Electrical drawing.
- Electrical engineer.
- Glossary of electrical terms.
 External references
- BS 5266-1.
- BS 5839-1.
- BS 7346-6.
- BS EN 50200:2006.
Featured articles and news
Our servers have reached another milestone. Why not write an article and be seen by our 6.5 million users.
RSHP celebrates competition win in Paris.
All about approved inspectors.
Whilst apparently confusing, German conservation is actually not that different.
The rise and fall of council housing. Book review.
Drivers of change in global heating markets.
11 interesting facts about the use and nature of the material.
Will politicians ultimately fail to tackle Britain's structural challenges?
How self-certification can save time and money.
CIBSE updates Fire Safety Engineering guidance.
EA finds England's water companies are simply unacceptable.