- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 02 Oct 2020
Lifts for office buildings
- British Standard 5655 part 6.
- CIBSE Guide D.
- Transportation Systems in Buildings and British Council for Offices (BCO) best practice guide.
The criteria for design includes:
- Morning up-peak handling capacity.
- Occupation density.
- Average interval.
- Car occupancy.
- A staircase allowance.
Morning up-peak handling capacity is expressed as a percentage of the building’s designed population that needs to be moved in a five minute period. Historically, the general consensus estimated this at 15%. However, the increasing use of flexible hours has reduced mass arrival numbers and the introduction of sophisticated computer controls systems suggest that the 15% figure might be radically reduced.
A 2004 morning peak survey of nine West End and City of London office buildings by Stanhope (Lift performance and specification) concluded 6% of an assumed population using 14m2/person recorded actual reality. Furthermore the survey concluded that lunchtime patterns were more relevant as lifts are being utilised in both directions as people enter and leave the building simultaneously. The Stanhope survey suggested 7% is an adequate design capacity figure.
Occupation density should include a 15% allowance for absenteeism. Multiple tenancies occupy space more densely than single tenants and trading floors have particularly dense spatial requirements. 10m2 per person is a very conservative figure that matches British Standards. BCO however believe 14m2 to be more realistic for standard offices. NAO audits carried out in 1999 on public sector buildings suggested 19m2 per person was a realistic density figure.
 Average interval time
Average interval time is the theoretical time for a single lift to complete the cycle of receiving passengers on the ground floor, discharging them on the various upper floors and returning to the ground floor. Where there are banks of lifts, the average interval time is divided by the number of lifts in the group. These calculations are based on averages and not the upper limit. 20 to 30 seconds provides a range from standard to prestige.
Waiting times are not the same as average interval times:
- 75% car loading of a 30 second average interval time equals 22.5 seconds waiting time.
- 85% car loading of a 30 second average interval time equals 25.5 second waiting time.
- 5% down, 3% up 12:00 to 12:40 per 5 mins.
- 3% down, 3% up 12:40 to 13:20 per 5 mins.
- 3% down, 5% up 13:20 to 14:00 per 5 mins.
- Capacity factor: 60% of car rating.
- Average waiting time: 25 secs lunchtime.
- Inter-floor traffic: 1% of design population 12:00 to 14:00 hrs.
 Find out more
 Related articles on Designing Buildings Wiki
- British Council for Offices.
- Criteria for the choice of a structural system to be included in office specification.
- Lifting platform.
- Lift motor room.
- Lift Standards: EN 81-20 and EN 81-50.
- Lifts and Escalators: A Quality Perspective.
- Lift shaft.
- Office definition.
- Office space planning.
- Post Occupancy Evaluation: operational performance of a refurbished office building.
- Structural systems for offices.
- The importance of service lifts.
- The science of lifts.
- The world's fastest lifts.
 External references
- Stanhope position paper – Lift performance and specification published February 2004
Featured articles and news
Predictions about adequate post-pandemic IAQ in non-domestic buildings.
Government publishes plans to 'build back greener'.
The contentious nature of claims associated with cladding, fire safety and EWS1 forms.
ECA comments on low-carbon heating systems initiative and Heat and Buildings Strategy.
Cinders and other forms of domestic rubbish created filth but also generated great wealth.
CIC 2050 Group requests input to find out priorities for future industry leaders.
IHBC publishes response to consultation.
Institute applauds funding initiatives but presses for additional retrofit and tax measures.
The switch from analogue to digital has begun.