- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 12 May 2019
It consists of a hollow copper sphere painted matt black to absorb radiant heat, with a temperature sensor at its centre. When it reaches a steady state (after 15 minutes or so depending on the size of the globe and the environmental conditions) the heat exchanges by convection and radiation will be in equilibrium, and the temperature recorded by the sensor will be somewhere between the air and radiant temperature. This is referred to as the globe temperature (tg) or black globe temperature and resembles the thermal conditions felt by the human body.
MRT = tg + 2.42 x air velocity in m/s (globe temperature – air temperature)
(equation ref Novalynx Corporation 2010 - this equation is dependent on the size and emissivity of the globe thermometer, and the units they show for air velocity are incorrect - cm/s, rather than the correct m/s shown above)
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
Bamboo pavilion built at London South Bank Uni.
Bringing in an expert.
Why the lowest price isn't sustainable.
The Most Economically Advantageous Tender.
Pipe dream or possibility?
The New Rules of Measurement.
Prioritising Sustainable Development Goals on projects.
The Architects Registration Board.
How BSRIA monitored the performance of new homes.