- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 16 Sep 2020
It consists of a hollow copper sphere painted matt black to absorb radiant heat, with a temperature sensor at its centre. When it reaches a steady state (after 15 minutes or so depending on the size of the globe and the environmental conditions) the heat exchanges by convection and radiation will be in equilibrium, and the temperature recorded by the sensor will be somewhere between the air and radiant temperature. This is referred to as the globe temperature (tg) or black globe temperature and resembles the thermal conditions felt by the human body.
MRT = tg + 2.42 x air velocity in m/s (globe temperature – air temperature)
(equation ref Novalynx Corporation 2010 - this equation is dependent on the size and emissivity of the globe thermometer, and the units they show for air velocity are incorrect - cm/s, rather than the correct m/s shown above)
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
The principles and art of the possible. Book review.
From horse and cart to hypermarket.
How elements and processes work together in a systems approach.
CIOB offers digital guide to proactive methods of working.
Tech will drive professional development in fields tied to infrastructure.
The idea for the structure emerged from the architect's dream.
Changing air tightness requirements prompt testing and revisions.
Government takes steps to revise building safety legislation.
Product can be 'grown' into bricks or used as a self-healing building material.
Anticipating COVID-19's continuing construction disruptions.
Availability payment arrangements involve project performance.
EU responds to COVID-19 with NextGenerationEU plan.