- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 30 Dec 2021
An ‘ambient loop’ is: ‘…a heat sharing network at a low temperature that can be used to share heat between floors of buildings, or between different buildings. An ambient loop can be used to and make use of waste heat between buildings. E.g. an office building’s air conditioning system can reject heat an ambient loop, (rather than atmosphere), this heat can then be used by a neighbouring residential development.’
Ref ‘Climate Emergency Design Guide: How new buildings can meet UK climate change’, published by The London Energy Transformation Initiative (LETI) in January 2020.
- A technical guide to district heating (FB 72).
- Air conditioning.
- Ambient network HVAC.
- BSRIA guide to heat interface units.
- Climate Emergency Design Guide.
- Combined heat and power.
- Community energy network.
- District energy networks.
- Geothermal energy.
- Heat interface units.
- Heat meter.
- Heat network.
- National heat map.
Featured articles and news
Activities summarised by the Construction Industry Council.
How Islamic architecture shaped Europe. Book review.
The campaign to preserve a rare blacksmith bridge.
Transitional options for the next generation of heating technologies.
Additional support being offered to job seekers with autism.
BSRIA adds to its series of illustrated guides.
ECA calls for energy levy reform.
ICE considers creation of new professional designation.
Principles of conservation for bronze objects. Book review.