- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 02 Feb 2020
An ‘ambient loop’ is: ‘…a heat sharing network at a low temperature that can be used to share heat between floors of buildings, or between different buildings. An ambient loop can be used to and make use of waste heat between buildings. E.g. an office building’s air conditioning system can reject heat an ambient loop, (rather than atmosphere), this heat can then be used by a neighbouring residential development.’
Ref ‘Climate Emergency Design Guide: How new buildings can meet UK climate change’, published by The London Energy Transformation Initiative (LETI) in January 2020.
 Related articles on Designing Buildings Wiki
- A technical guide to district heating (FB 72).
- Air conditioning.
- BSRIA guide to heat interface units.
- Climate Emergency Design Guide.
- Combined heat and power.
- Community energy network.
- District energy networks.
- Geothermal energy.
- Heat interface units.
- Heat meter.
- Heat network.
- National heat map.
Featured articles and news
Smart mapping approaches for building better infrastructure.
The importance of emergency planning.
Eight forms of resource optimisation.
CIOB responds to Chancellor Sunak's announcement on jobs and the economy.
Revised guide to competition rules available.
Brick slip soffit systems and intricate brick features.
An innovative engineering approach could have had tragic consequence for NYC.
Some secrets behind how canals work.
Breaking down possible steps of pre-contract management.
ICE event includes comments from Welsh Government Minister Julie James.
Designing Buildings Wiki becomes the world's first website to adopt the new knowledge standard.