- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 09 Nov 2020
Place of special fire risk
The Scottish Building Standards, Part I. Technical Handbook – Domestic, Appendix A Defined Terms, defines a place of special fire risk as:
- solid fuel appliances, with a total installed output rating more than 50 kW, other than kitchen appliances or
- oil or gas fired appliances, with a total installed net input rating more than 70 kW, other than kitchen appliances and forced air convection or radiant heaters in buildings which are neither residential nor domestic or
- fixed internal combustion engines, including gas turbine engines, with a total output rating more than 45 kW or
- oil-immersed electricity transformers or switch gear apparatus with an oil capacity more than 250 litres and operating at a supply voltage more than 1000 volts or
- fuel oil storage tanks having a capacity of more than 90 litres or
- paint spray booths or rooms where cellulose or other flammable liquid spray is used.’
 Related articles on Designing Buildings Wiki
Featured articles and news
Guidance offered on COVID-19 green recovery, building safety and more.
Providing strength and support above the joists.
Enforcer will test and investigate product safety.
Underfloor air conditioning comes to 24 St James's Square.
Consultation on public right to buy unused public property.
IHBC resource offers improved consistency.
New laws to ‘retain and explain’ historic statues.
The principles and art of the possible. Book review.
From horse and cart to hypermarket.
How elements and processes work together in a systems approach.
CIOB offers digital guide to proactive methods of working.
Tech will drive professional development in fields tied to infrastructure.