- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 09 Nov 2020
Place of special fire risk
The Scottish Building Standards, Part I. Technical Handbook – Domestic, Appendix A Defined Terms, defines a place of special fire risk as:
- solid fuel appliances, with a total installed output rating more than 50 kW, other than kitchen appliances or
- oil or gas fired appliances, with a total installed net input rating more than 70 kW, other than kitchen appliances and forced air convection or radiant heaters in buildings which are neither residential nor domestic or
- fixed internal combustion engines, including gas turbine engines, with a total output rating more than 45 kW or
- oil-immersed electricity transformers or switch gear apparatus with an oil capacity more than 250 litres and operating at a supply voltage more than 1000 volts or
- fuel oil storage tanks having a capacity of more than 90 litres or
- paint spray booths or rooms where cellulose or other flammable liquid spray is used.’
 Related articles on Designing Buildings Wiki
Featured articles and news
Organisation alerts membership to findings of IHBC research.
Four outstanding professionals recognised.
Sustainable flooring from super strong grass.
Organisation presents reactions from industry leaders.
New infrastructure bank to be based in the North of England.
Fairer, faster, greener. A summary of the key points.
Strategies to help provide safer working conditions.
Protecting flora, fauna and the other natural features of Scotland.
Architecture considered somewhere between 'sublime and beautiful'.
Polish piano factory revived through an energy-oriented tune up.
Dynamic architectural approach sets out to restore and improve the environment.
Entries accepted from 1 December 2020 to 14 April 2021.
Procedure discontinued for sale or re-mortgage of buildings without cladding.