- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 09 Nov 2020
Place of special fire risk
The Scottish Building Standards, Part I. Technical Handbook – Domestic, Appendix A Defined Terms, defines a place of special fire risk as:
- solid fuel appliances, with a total installed output rating more than 50 kW, other than kitchen appliances or
- oil or gas fired appliances, with a total installed net input rating more than 70 kW, other than kitchen appliances and forced air convection or radiant heaters in buildings which are neither residential nor domestic or
- fixed internal combustion engines, including gas turbine engines, with a total output rating more than 45 kW or
- oil-immersed electricity transformers or switch gear apparatus with an oil capacity more than 250 litres and operating at a supply voltage more than 1000 volts or
- fuel oil storage tanks having a capacity of more than 90 litres or
- paint spray booths or rooms where cellulose or other flammable liquid spray is used.’
 Related articles on Designing Buildings Wiki
Featured articles and news
Recognising past and present role models for the future.
So why not write something?
LETI publishes guidance for energy efficient home retrofits.
Predictions about adequate post-pandemic IAQ in non-domestic buildings.
Government publishes plans to 'build back greener'.
The contentious nature of claims associated with cladding, fire safety and EWS1 forms.
ECA comments on low-carbon heating systems initiative and Heat and Buildings Strategy.
Cinders and other forms of domestic rubbish created filth but also generated great wealth.
CIC 2050 Group requests input to find out priorities for future industry leaders.