- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 09 Oct 2017
Place of special fire hazard
- Oil-filled transformer and switch gear rooms.
- Boiler rooms.
- Storage spaces for fuel or other highly-flammable substances.
- Rooms housing a fixed internal combustion engine.
A protected lobby should be provided between an escape stairway and a place of special fire hazard. The lobby should have not less than 0.4m² permanent ventilation, or should be protected from the ingress of smoke by a mechanical smoke control system.
 Related articles on Designing Buildings Wiki
Featured articles and news
Conservation in the heritage cities of Venice and Liverpool.
Which room is the most fun to design? Find out the 'Grand Designs' presenter's unusual choice in our interview.
Full suite of speakers are announced for this year's BSRIA Briefing event.
Book your place for the Architectural Technology Awards 2018.
There are many ways of classifying types of building. Have a look at our range of building articles.
BSRIA have launched the 'major update' of the go-to design framework guide for building services.
How to get results with building life cycle assessment.
Government publishes a prospectus inviting proposals for new 'garden communities'.
The Morandi motorway bridge in Genoa collapses during rainstorm while undergoing maintenance works.
'Developed design' is a phrase coined by the RIBA for their 2013 Plan of Work. But what does it actually mean?
New green paper published aiming to rebalance the relationship between landlords and residents and tackle stigma.