- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 28 Jul 2021
Luminaire efficacy is the ‘Light output of an entire luminaire divided by the total power consumed by the lamps and ballasts. Equal to the lamp efficacy multiplied by the light output ratio of the luminaire.’
Ballast or control gear, is ‘Part of the control equipment of fluorescent or discharge lamps, used to stabilise the current. The older, traditional main-frequency ballast can consume up to 20-25% of the total lamp current. A modern electronic ballast working at high frequency consumes about 30% less current, and can be used to regulate or dim the lamp output.’
 Related articles on Designing Buildings Wiki
- Ballast or control gear.
- Colour appearance.
- Colour Rendering Index CRI.
- Daylight benefits in healthcare buildings.
- Daylight factor.
- Daylight lighting systems.
- Dichroic reflector.
- Discharge lamp.
- Extra-low voltage lamps.
- General lighting v task lighting.
- Lamp efficacy.
- Lighting energy numeric indicator LENI.
- Lighting of construction sites.
Featured articles and news
Global building automation and control systems trends reviewed.
Significant changes to BS 7671:2018+A2:2022 announced.
Students available for administrative roles.
Delisting a World Heritage Site.
Design needs to be more diverse to be widely accessible.
It’s not always a case of the centre leading.
PHribbon toolbar developed for US market.
CIOB consultation seeks feedback on APPG 2020 report.
How to respond to changes made in the October 2021 update.