- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 09 Feb 2017
Lighting energy numeric indicator LENI
Changes to the approved documents for Part L of the building regulations came into effect on 6 April 2014 when the 2013 editions of approved documents L1A and L2A came into force along with 2013 amendments to the 2010 editions of approved documents L1B and L2B.
Approved documents L2A and L2B refer to the Non-domestic Building Services Compliance Guide 2013 edition which introduces the Lighting Energy Numeric Indicator (LENI) as an alternative means of demonstrating the compliance of lighting systems. This means that compliance can now be demonstrated either by meeting the recommended minimum standards for efficacy and building controls, or by meeting the recommended minimum standards for LENI.
The Lighting Energy Numeric Indicator was originally defined by BS EN 15193:2007, Energy performance of buildings. However, the calculation methodology set out in the Non-domestic Building Services Compliance Guide is a much simplified version.
LENI is an indicator of the efficiency of an entire lighting installation, including controls and is expressed in terms of energy per square metre per year (kWh/m2/yr). The calculated LENI must not exceed prescribed limit for a given illuminance and the number of hours per year the lighting will be required, as set out in Table 44 of the compliance guide.
LENI is calculated based on the level of illuminace in a particular area and the number of hours a year that the lighting will be required. The calculation takes into account:
- Energy used by any lighting control systems (parasitic energy use Ep).
- The total power of the lighting in watts (Pl).
- Energy saved by automatic control systems that switch off lights when rooms are empty (occupancy factor Fo).
- Energy saved by automatic control systems that dim lighting if daylight is available (Fd)
- The reduction in performance through the life of the system (constant illuminance factor Fc)
The LENI is the sum of energy use (daytime, night-time and parasitic energy use) divided by the area.
 Related articles on Designing Buildings Wiki
- 2013 changes to the approved documents for part L of the building regulations.
- Approved documents.
- Building regulations.
- Daylight lighting systems.
- Part L.
 External references
- Orlight, Guide on lighting risks and regulations, April 2014.
- Planning portal, Domestic and Non-domestic Building Services Compliance Guide, 2013 edition.
Featured articles and news
HAB is a bridge design concept which incorporates an integrated hydraulic system in order to carry more weight.
ICE publish a discussion paper looking at the role of the engineer in creating inclusive cities.
A PQP describes the activities, standards, tools and processes necessary to achieve quality in a project's delivery.
How Lidl has been actively working to reinforce their brand through sustainability.
Association of British Insurers describe full-scale cladding tests as 'utterly inadequate'.
This article examines the changing policy commitments and evolving definitions of the zero carbon home.
Researchers believe they may have created a 'game-changing' new form of concrete using graphene.
Grouting refers to the injection of materials into a soil or rock formation to change its physical characteristics.
Part of Designing Buildings Wiki, BREEAM Wiki will advance knowledge sharing for the BRE family of sustainability tools.
From the decorative to the utilitarian, and from the photographed to the forgotten.
New BRE book considers the progression from project-based knowledge creation to whole-life urban knowledge management.
This CIOB article explores the concept of value in building design and construction.