Lighting energy numeric indicator LENI
Changes to the approved documents for Part L of the building regulations came into effect on 6 April 2014 when the 2013 editions of approved documents L1A and L2A came into force along with 2013 amendments to the 2010 editions of approved documents L1B and L2B.
Approved documents L2A and L2B refer to the Non-domestic Building Services Compliance Guide 2013 edition which introduces the Lighting Energy Numeric Indicator (LENI) as an alternative means of demonstrating the compliance of lighting systems. This means that compliance can now be demonstrated either by meeting the recommended minimum standards for efficacy and building controls, or by meeting the recommended minimum standards for LENI.
This was a change that had been campaigned for by the lighting industry to bring lighting design into alignment with European standards and to give designers greater flexibility.
The Lighting Energy Numeric Indicator was originally defined by BS EN 15193:2007, Energy performance of buildings. However, the calculation methodology set out in the Non-domestic Building Services Compliance Guide is a much simplified version.
LENI is an indicator of the efficiency of an entire lighting installation, including controls and is expressed in terms of energy per square metre per year (kWh/m2/yr). The calculated LENI must not exceed prescribed limit for a given illuminance and the number of hours per year the lighting will be required, as set out in Table 44 of the compliance guide.
LENI is calculated based on the level of illuminace in a particular area and the number of hours a year that the lighting will be required. The calculation takes into account:
- Energy used by any lighting control systems (parasitic energy use Ep).
- The total power of the lighting in watts (Pl).
- Energy saved by automatic control systems that switch off lights when rooms are empty (occupancy factor Fo).
- Energy saved by automatic control systems that dim lighting if daylight is available (Fd)
- The reduction in performance through the life of the system (constant illuminance factor Fc)
The LENI is the sum of energy use (daytime, night-time and parasitic energy use) divided by the area.
 Related articles on Designing Buildings Wiki
- 2013 changes to the approved documents for part L of the building regulations.
- Approved documents.
- Building regulations.
- Daylight lighting systems.
- Part L.
 External references
- Orlight, Guide on lighting risks and regulations, April 2014.
- Planning portal, Domestic and Non-domestic Building Services Compliance Guide, 2013 edition.
Featured articles and news
Why buildings crack, how cracks are categorised and what can be done.
Inaugurated last week, the new Elbphilharmonie concert venue; a soaring new addition to Hamburg's skyline.
Summary of a new ICE Transport journal which says improving transport infrastructure is essential to eradicating global poverty.
BRE look at a new government report into the accuracy of heat meters.
Herzog & de Meuron get planning permission for revamp of Chelsea FC football stadium.
UK-GBC green paper proposes more powers for cities on new-build housing.
The Pompidou Centre – not a monument but an event.
The Chartered Institute of Building restructures and launches 29 new local hubs.
Designing Buildings Wiki talks to the founder of the world's first indoor biophilic gym, now open in London.
£1.3bn Swansea Bay project to be backed as a 'pathfinder' for other tidal lagoon projects.
Designs released for a proposed Las Vegas stadium to entice the Oakland Raiders.
Have a look at these award-winning concept designs for a thermal bath in Latvia.