- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 09 Feb 2017
Lighting energy numeric indicator LENI
Changes to the approved documents for Part L of the building regulations came into effect on 6 April 2014 when the 2013 editions of approved documents L1A and L2A came into force along with 2013 amendments to the 2010 editions of approved documents L1B and L2B.
Approved documents L2A and L2B refer to the Non-domestic Building Services Compliance Guide 2013 edition which introduces the Lighting Energy Numeric Indicator (LENI) as an alternative means of demonstrating the compliance of lighting systems. This means that compliance can now be demonstrated either by meeting the recommended minimum standards for efficacy and building controls, or by meeting the recommended minimum standards for LENI.
The Lighting Energy Numeric Indicator was originally defined by BS EN 15193:2007, Energy performance of buildings. However, the calculation methodology set out in the Non-domestic Building Services Compliance Guide is a much simplified version.
LENI is an indicator of the efficiency of an entire lighting installation, including controls and is expressed in terms of energy per square metre per year (kWh/m2/yr). The calculated LENI must not exceed prescribed limit for a given illuminance and the number of hours per year the lighting will be required, as set out in Table 44 of the compliance guide.
- Energy used by any lighting control systems (parasitic energy use Ep).
- The total power of the lighting in watts (Pl).
- Energy saved by automatic control systems that switch off lights when rooms are empty (occupancy factor Fo).
- Energy saved by automatic control systems that dim lighting if daylight is available (Fd)
- The reduction in performance through the life of the system (constant illuminance factor Fc)
 Find out more
 Related articles on Designing Buildings Wiki
- 2013 changes to the approved documents for part L of the building regulations.
- Approved documents.
- Building regulations.
- Daylight lighting systems.
- Part L.
 External references
- Orlight, Guide on lighting risks and regulations, April 2014.
- Planning portal, Domestic and Non-domestic Building Services Compliance Guide, 2013 edition.
Featured articles and news
Securing suitable water systems.
Love them or hate them, they are popping up everywhere.
The initiative to enhance the environment continues.
Could underused community spaces offer an alternative to working from home?
Keeping workers and workplaces safe in the United States.
A history lesson in geographic information systems.
A low tech, easy to use method of extinguishing small fires.
How can these valued spaces be reused?
Partnership avoids the need for listed building consent.
Connecting building design from inception to completion to operations.
Gregor Harvie predicts interoperability will be construction’s Uber moment.
Expert commentary and insight.
Guidance offered for stained glass window maintenance.
Define need before determining viability.