- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 04 Sep 2017
Checking oil tanks
When relying on an oil tank for the main source of central heating, it is crucial that it is checked regularly for leaks, corrosion and other signs of delay. Once an oil tank has started to deteriorate, repairs should be made as soon as possible before serious damage is done.
Although oil tanks are built to withstand normal weathering, there are a number of issues to look out for to ensure they remain in good condition, to ensure longevity and to avoid environmental spills from leaks.
This article describes some of the more common occurrences that can be recognised by sight, how these might affect the oil tank and what should be done to resolve these issues.
 Signs of problems
Rust is fairly easy to identify as it shows on the tank exterior and can be flaky or cause blistering of paint. A rusting oil tank can be dangerous as the rust will worsen over time, potentially leading to environmental spills and also perhaps polluting the oil itself, making it less efficient. Rust is only present in metal tanks, however those with plastic oil tanks must check the plastic for any whitening, cracking or splits or any bulging in the tank profile as this can be equally as dangerous.
Leaking joints Cleaning up a leak of heating fuel from a domestic storage tank can be very expensive, so checking for leaking joints is essential. A key sign of an oil leak or a leaking joint is that oil usage suddenly increases unexpectedly. It is important to check the tank and pipework as soon as this is noticed, or purchase a tank monitoring device that can give an early warning of a rapid drop in oil level.
Water or sludge in the tank
Tanks containing water or sludge can clog the pipework and damage or even corrode heating systems, which reduces the oil efficiency and ultimately makes your heating cost more. You can find out whether or not your tank has water or sludge in it by looking for a ‘darkened’ area at the bottom of the tank, or by using water-finding paste which needs to be attached to a long stick and then placed into a tank. The colour of the paste will determine whether or not water is present.
Conducting regular checks will help to reduce the risk of a large repair bill if something is wrong. In addition, an annual check-up by a qualified professional will provide more detail on condition and maintenance requirements.
If you are not entirely sure as to the condition of your oil tank, or if you see something suspicious that you want to know more about, seek advice from a licensed professional.
Featured articles and news
Which room is the most fun to design? Find out the 'Grand Designs' presenter's unusual choice in our interview.
Full suite of speakers are announced for this year's BSRIA Briefing event.
Book your place for the Architectural Technology Awards 2018.
There are many ways of classifying types of building. Have a look at our range of building articles.
BSRIA have launched the 'major update' of the go-to design framework guide for building services.
How to get results with building life cycle assessment.
Government publishes a prospectus inviting proposals for new 'garden communities'.
The Morandi motorway bridge in Genoa collapses during rainstorm while undergoing maintenance works.
'Developed design' is a phrase coined by the RIBA for their 2013 Plan of Work. But what does it actually mean?
New green paper published aiming to rebalance the relationship between landlords and residents and tackle stigma.
RIBA calls for a comprehensive ban on combustible materials.