- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 13 Jul 2021
Multiple-station smoke alarm
The 2018 International Residential Code (IRC), published by the International Code Council (ICC) defines a multiple-station smoke alarm as: ‘Two or more single-station alarm devices that are capable of interconnection such that actuation of one causes all integral or separate audible alarms to operate.’
 Related articles on Designing Buildings Wiki
- Smoke alarm.
- Domestic smoke alarms DG525.
- Fire detection and alarm system.
- Fire detector.
- Heat alarm.
- Ionisation smoke alarm.
- Multi-sensor alarm.
- Optical smoke alarm.
- Single-station smoke alarm.
- Smoke detection in high ceiling spaces.
- Smoke barrier.
- The causes of false fire alarms in buildings.
Featured articles and news
What will it take to stop it ?
To celebrate world bee day 2022 !
Not forgetting part F and the new part overheating part O.
As energy prices jump up in cost.
With people in the UK from Ukraine.
Industry leader Steve Murray takes on role.
An abundant and versatile building material.
600,000 heat pump installations targeted per year by 2028.
Helping prevent those unwanted outcomes.
How has transport changed due to Covid-19 ?
Will you need it ? after June 15 and the new Part O ?
Create an account and write the first of many articles.
CIAT commentary after the first meeting.
Who is to blame?
Research recommends focussing on portfolio success rather than project success.
The revised standard for mapping underground utilities.
Cross-industry steering group seeks support in delivery.