- Project plans
- Project activities
- Legislation and standards
- Industry context
- Specialist wikis
Last edited 16 Dec 2020
Local manual switching
Local manual switching means: ‘…the distance on plan from any local switch to the luminaire it controls should generally be not more than 6 m, or twice the height of the light fitting above the floor if this is greater. Where the space is a daylit space served by side windows, the perimeter row of lighting should in general be separately switched.’
Ref Non-domestic Building Services Compliance Guide For Scotland, 2015 Edition v1.1, published by the Scottish Government, Building Standards Division in April 2018.
 Related articles on Designing Buildings Wiki
Featured articles and news
PHribbon toolbar developed for US market.
CIOB consultation seeks feedback on APPG 2020 report.
How to respond to changes made in the October 2021 update.
Resource provides professional installation assistance.
Adaptive planning proposal spans 15 years.
Activities summarised by the Construction Industry Council.
How Islamic architecture shaped Europe. Book review.
The campaign to preserve a rare blacksmith bridge.
Transitional options for the next generation of heating technologies.