- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 18 Dec 2015
Wet bulb globe temperature
Heat stress is a form of overheating that the occupants of a building may experience when the measures their bodies use to regulate internal temperature begin to fail. This can occur, for example, in buildings where an industrial process is being carried out, such as smelting, brick-firing, cooking and so on.
Heat stress is dependent on a number of factors, such as air temperature, metabolic rate, humidity, clothing, length of exposure, acclimatisation and so on. This means that it is a personal condition. Some occupants may experience heat stress whilst others may not.
Where humidity is high, or occupants are wearing protective clothing that cannot be adjusted or removed, the body may be unable to lose heat through the evaporation of sweat and so the individual may begin to experience elevated deep-body temperature, excessive sweating and increased heart rate. This can cause; dehydration, headache, difficulty concentrating, confusion, muscle cramp, heat rash, fatigue, giddiness, fainting, nausea, convulsions and ultimately, if it is allowed to persist, death.
The Workplace Regulations, the Management of Health and Safety at Work Regulations 1999 require that employers assess the risks to the health and safety of their workers, and take action where necessary and reasonably practicable.
Wet bulb globe temperature is a relatively simple indicator of heat stress. It includes components of natural wet-bulb temperature (tnw), globe temperature (tg) and air temperature (ta - dry bulb temperature).
- Where there is no solar radiation, wet bulb globe temperature = 0.7tnw + 0.3tg
- Where there is solar radiation, wet bulb globe temperature = 0.7tnw +0.2tg +0.1ta
The recorded values can be compared to recommended values for a specific metabolic rate and state of acclimatisation (found in BS EN 27243:1994, ISO 7243 Hot environments. Estimation of the heat stress on working man, based on the WBGT-index (wet bulb globe temperature)).
However, this will only provide an indication of whether heat stress is likely. Wet bulb globe temperature is a compromise, offering a measure that is relatively simple to assess, whilst still recording the key components of heat stress. Where the recomended values are exceeded, a more accurate measure such as Required Sweat Rate (also found in BS EN 12515) should be used for further assessment.
 Find out more
 Related articles on Designing Buildings Wiki
- Dry bulb temperature.
- Globe temperature.
- Heat stress.
- Operative temperature.
- Relative humidity.
- Thermal comfort.
- Wet bulb temperature.
 External references
- HSE, Heat stress.
- BS EN 27243:1994, ISO 7243 Hot environments. Estimation of the heat stress on working man, based on the WBGT-index (wet bulb globe temperature).
Featured articles and news
When is there a right to light, and what happens if it is obstructed?
What would the nationalisation of economic infrastructure mean for GB?
A new guide to improving value by reducing design error.
We've reached 80,000 page views a day and 10,000 registered users. Why not join them?
A masterplan is a framework within which a location is encouraged to develop or change. Read our introductory article.
New consultation announced on a specialist Housing Court to settle landlord-tenant disputes.
ICE responds to a transport consultation advising the government to make decisions enabling more inclusive cities.
BRE and Loughborough University complete first phase refurbishment of demonstration home.
How the risk of collapse of fibrous plaster ceilings is being addressed in theatres.
If you’re a great writer and have practical experience of the construction industry, it could be you.
Frustrated by long documents or technical jargon? Put off by sign-up forms or costs? Take this 5 min survey to help improve construction knowledge.