Wet bulb globe temperature
Heat stress is a form of overheating that the occupants of a building may experience when the measures their bodies use to regulate internal temperature begin to fail. This can occur, for example, in buildings where an industrial process is being carried out, such as smelting, brick-firing, cooking and so on.
Heat stress is dependent on a number of factors, such as air temperature, metabolic rate, humidity, clothing, length of exposure, acclimatisation and so on. This means that it is a personal condition. Some occupants may experience heat stress whilst others may not.
Where humidity is high, or occupants are wearing protective clothing that cannot be adjusted or removed, the body may be unable to lose heat through the evaporation of sweat and so the individual may begin to experience elevated deep-body temperature, excessive sweating and increased heart rate. This can cause; dehydration, headache, difficulty concentrating, confusion, muscle cramp, heat rash, fatigue, giddiness, fainting, nausea, convulsions and ultimately, if it is allowed to persist, death.
The Workplace Regulations, the Management of Health and Safety at Work Regulations 1999 require that employers assess the risks to the health and safety of their workers, and take action where necessary and reasonably practicable.
Wet bulb globe temperature is a relatively simple indicator of heat stress. It includes components of natural wet-bulb temperature (tnw), globe temperature (tg) and air temperature (ta - dry bulb temperature).
- Where there is no solar radiation, wet bulb globe temperature = 0.7tnw + 0.3tg
- Where there is solar radiation, wet bulb globe temperature = 0.7tnw +0.2tg +0.1ta
The recorded values can be compared to recommended values for a specific metabolic rate and state of acclimatisation (found in BS EN 27243:1994, ISO 7243 Hot environments. Estimation of the heat stress on working man, based on the WBGT-index (wet bulb globe temperature)).
However, this will only provide an indication of whether heat stress is likely. Wet bulb globe temperature is a compromise, offering a measure that is relatively simple to assess, whilst still recording the key components of heat stress. Where the recomended values are exceeded, a more accurate measure such as Required Sweat Rate (also found in BS EN 12515) should be used for further assessment.
 Related articles on Designing Buildings Wiki
- Dry bulb temperature.
- Globe temperature.
- Heat stress.
- Operative temperature.
- Relative humidity.
- Thermal comfort.
- Wet bulb temperature.
 External references
- HSE, Heat stress.
- BS EN 27243:1994, ISO 7243 Hot environments. Estimation of the heat stress on working man, based on the WBGT-index (wet bulb globe temperature).
Featured articles and news
Read about Belgrade's Brutalist landmark - the Western City Gate.
Read about the measures that can be taken by individuals to protect and minimise exposure to outdoor sourced air pollution.
Government announces leaseholds on new-build houses will be banned.
Transport Secretary announces public consultation into London's funding of Crossrail 2.
Have a look at some of the most impressive concert stage designs of all time, including Pink Floyd, U2, Rolling Stones, and more...
What is the Home Quality Mark? Find out how it can help you when buying/renting a new home.
Business Secretary launches £246m Faraday Challenge to establish UK as world leader in battery technology.
Government announces new plans for regulations to improve safety and security awareness of drone users.
Read our introductory article to the various different types of fuel.
IHBC book review: Charles Barry’s monumental struggle to rebuild the Houses of Parliament.
Read about RSHP's British Museum extension which has been shortlisted for the 2017 Stirling Prize.
Read our introductory article to building a house extension.
More updates from DCMS about the large-scale testing of cladding systems and the number of buildings affected.
UandI secure resolution to grant planning consent for major new regeneration project.