- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 20 Apr 2018
Draught diverter v draught stabiliser
A draught diverter is a form of draught break intended to prevent conditions in the main length of flue from interfering with the combustion performance of an open-flued appliance. It allows the appliance to operate without interference from down-draughts that may occur in adverse wind conditions and excessive draught.
A draught stabiliser is a factory-made counter-balanced flap device admitting air to the flue, from the same space as the combustion air, to prevent excessive variations in the draught. It is usual for these to be in the fluepipe or chimney, but they may be located on the appliance.
NB A 'draught break' is an opening formed by a factory-made component into any part of the flue serving an open-flued appliance. Such openings may be provided to allow dilution air to be drawn into a flue or to lessen the effects of down-draught on combustion in the appliance.
 Find out more
 Related articles on Designing Buildings Wiki
Featured articles and news
Brick slip soffit systems and intricate brick features.
Breaking down possible steps of pre-contract management.
ICE event includes comments from Welsh Government Minister Julie James.
How to write them and what they should include.
Designing Buildings Wiki becomes the world's first website to adopt the new knowledge standard.
Assessing the most beneficial design elements.
Exploring different types of vinyl flooring.
New Government task force will build beauty into reformed planning process.
Five outstanding aspects of the profession.
The seismic strengthening of historic churches.
Results show guarded optimism and payment concerns.
Noteworthy navigable aqueducts.