- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 12 Nov 2020
Heating degree days
Heating degree days (HDD) are used to give an indication of the effect of outside air temperature on building energy consumption during a specified period of time. They represent the number of degrees and number of days that the outside air temperature at a specific location is lower than a specified base temperature (or balance point). This gives an indication of how much heating will be required in the building.
So for example, if the base temperature of a building is 21 degrees, and the outside air temperature is 12 degrees for eight hours (one third of a day), then that represents 3 heating degree days ((21-12) x 1/3 = 3).
Adding up heating degree days can give a weekly, monthly or annual figure.
Heating degree days calculated for locations with publicly available meteorological data and so it is necessary to locate an accurate weather station, with good historical data close to the site being investigated, or in circumstances similar to the site being investigated. Weather station data such as that available from airports is often considered to be the highest quality.
Data is also available to allow calculation of ‘cooling degree days’ representing the number of degrees and days the outside temperature is above the base temperature and ‘growing degree days’, based on the temperature range within which plants will grow.
Heating and cooling degree days can be used to help assess or compare different potential sites for development. They can also be used as a way of normalising weather between different sites, allowing comparison of the performance of different buildings, or for normalising weather between different years to assess changes in the performance of a building.
There can be difficulty separating out heating and cooling energy consumption from overall energy consumption, and heating and cooling requirements are influenced by other factors such as; other heat sources (including people, lighting, equipment and solar gain), thermal mass, thermal insulation and so on. In addition, heating and cooling inputs tend to be intermittent rather than continuous, and buildings are not necessarily always occupied.
It is possible to take account of these matters in calculations and through the use of sub-metering, but this can become a very complicated process, based on a deceptively simple indicator. The use of degree days should therefore be treated with caution, employed as part of a broader process of analysis and assessment providing only a general indicator for order of magnitude assessments rather than accurate detailed comparisons.
 Find out more
 Related articles on Designing Buildings Wiki
- Cooling degree days.
- Comfort in low energy buildings.
- Computational fluid dynamics.
- Energy targets.
- Heat stress.
- Passive building design.
- Post occupancy evaluation.
- Solar gain.
- Thermal comfort.
- Thermal indices.
- Urban heat island effect.
 External references
Featured articles and news
IHBC resource offers improved consistency.
New laws to ‘retain and explain’ historic statues.
The principles and art of the possible. Book review.
From horse and cart to hypermarket.
How elements and processes work together in a systems approach.
CIOB offers digital guide to proactive methods of working.
Tech will drive professional development in fields tied to infrastructure.
The idea for the structure emerged from the architect's dream.
Changing air tightness requirements prompt testing and revisions.
Government takes steps to revise building safety legislation.
Product can be 'grown' into bricks or used as a self-healing building material.
Anticipating COVID-19's continuing construction disruptions.