It consists of a hollow copper sphere painted matt back to absorb radiant heat, with a temperature sensor at its centre. When it reaches a steady state (after 15 minutes or so depending on the size of the globe and the environmental conditions) the heat exchanges by convection and radiation will be in equilibrium, and the temperature recorded by the sensor will be somewhere between the air and radiant temperature. This is referred to as the globe temperature (tg) or black globe temperature and resembles the thermal conditions felt by the human body.
MRT = tg + 2.42 x air velocity in cm/s (globe temperature – air temperature)
 Related articles on Designing Buildings Wiki
Featured articles and news
Sadiq Khan publishes a new development strategy for the capital.
In the week of the momentous Heathrow decision, we look back at the development and design of T5.
BSRIA’s flagship event will address performance and wellbeing beyond compliance.
Young Architects and Developers Alliance launched to build the relationship between the two disciplines.
BS 8536-2:2016 Design and construction: Code of practice for asset management (Linear and geographical infrastructure).
Paying for off-site goods or materials can be useful, but it puts the client at risk.
People power can be transformative if properly informed and inspired.
ZHA win competition to build an Urban Heritage Administration Centre in Saudi Arabia.
Leaps, not steps, are needed to avoid a ticking time bomb, say BRE in response to Farmer Review.
A multi-purpose hall in France covered in a translucent orange membrane.
Winning designs revealed for a rock formation-influenced residential complex in Rennes.
An article explaining the techniques, regulations and environmental impacts of carbon capture and storage.
Watch one of the first documentaries by the acclaimed Adam Curtis, examining the substandard system building of the 1960s.