Operative temperature (previously known as resultant temperature or dry resultant temperature, but renamed to align with ASHRAE and ISO standards) is a simplified measure of human thermal comfort derived from air temperature, mean radiant temperature and air speed. It can be useful in assessing the likely thermal comfort of the occupants of a building.
Actual thermal comfort is dependent on environmental factors, such as air temperature, air velocity, relative humidity and the uniformity of conditions, as well as personal factors such as clothing, metabolic heat, acclimatisation, state of health, expectations, and even access to food and drink. However as empirical fits to these variables are very complex (see predicted mean vote), a simpler measure can be more useful in practice.
Operative temperature is defined as:
Operative temperature = (tr + (ta x √10v)) / (1+√10v)
ta = air temperature
v = air speed (m/s)
Operative temperature = (( hr x tr) + (hc x ta )) / ( hr + hc )
hc = convective heat transfer coefficient
hr = radiative heat transfer coefficient
Where the air speed is less than 0.1m/s, (as is typical in buildings) radiative and convective heat transfers may be similar, and so the equation can be simplified to:
Operative temperature = (ta + tr)/2
In many spaces, with low air velocity and where air temperature and mean radiant temperature may be similar, air temperature alone can be a reasonable indicator of thermal comfort. However, in spaces where surfaces may be heated or cooled, where there is significant thermal mass, or where solar radiation is present, air and radiant temperatures may be very different and so it is necessary to take account of radiant temperatures in assessing thermal comfort.
 Related articles on Designing Buildings Wiki
Featured articles and news
Paying for off-site goods or materials can be useful, but it puts the client at risk.
People power can be transformative if properly informed and inspired.
ZHA win competition to build an Urban Heritage Administration Centre in Saudi Arabia.
Leaps, not steps, are needed to avoid a ticking time bomb, say BRE in response to Farmer Review.
A multi-purpose hall in France covered in a translucent orange membrane.
Winning designs revealed for a rock formation-influenced residential complex in Rennes.
An article explaining the techniques, regulations and environmental impacts of carbon capture and storage.
Watch one of the first documentaries by the acclaimed Adam Curtis, examining the substandard system building of the 1960s.
Take a look at the tech start-up that could transform construction design and communication.
This house in Barcelona uses an innovative new facade tiling system to blend into the landscape.
The origins, evolution and future of Level 3 BIM.