- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 27 Jun 2014
A thermal labyrinth decouples thermal mass from the occupied space, usually by creating a high thermal mass concrete undercroft with a large surface area. Decoupling the thermal mass means it can be cooled to a lower temperature than if it was in the occupied space.
This stored ‘coolth’ can be used to condition the space in hot periods.
The labyrinth layout needs to balance optimum thermal storage with the air resistance of the system. Creating air turbulence, by increasing the roughness and incorporating bends, improves heat transfer. However, incorporating too many bends may increase the air resistance beyond the point where the system can be part of a passive or naturally ventilated scheme.
 Size and output
As labyrinths are often constructed directly beneath a building, only the sides and floor of the labyrinth are in contact with the earth and the top of the labyrinth is directly coupled with the building. This means that the labyrinth needs to be well insulated from the building to prevent heat transfer.
The earth contact of the labyrinth gives the benefit of steady ground temperatures, however, the undisturbed ground temperature cannot be used in calculations, as it will be affected by the presence of the building and the operation of the labyrinth. This means that optimisation of the design requires a complete thermal simulation of the system.
Regular inspection and cleaning of the labyrinth are recommended, although thermal labyrinths are generally virtually maintenance free. The major cost that can be incurred is when fan power is required to supply air through the labyrinth.
Thermal labyrinths can be integrated into a building's structure to provide free cooling in the summer and pre-heating of air in the winter. They can have high capital costs, but over the life of a building,
can yield substantial savings by reducing peak demand for cooling and heating.
This article was created by --Buro Happold, 17 March 2013, based on a 2008 article in 'Patterns'.
 Related articles on Designing Buildings Wiki
- Air source heat pumps.
- Dynamic thermal modelling of closed loop geothermal heat pump systems.
- Earth-to-air heat exchangers.
- Geothermal energy.
- Geothermal pile foundations.
- Ground energy options.
- Ground pre-conditioning of supply air.
- Ground source heat pumps.
- Thermal mass.
- Trombe wall.
 External references
- Ingenia, Going underground September 2006.
Featured articles and news
EIRs define what is needed from the employer's internal team and suppliers for project development.
The full keynote speech by Sir James Bevan, Environment Agency CEO, on the future of flood protection.
After 6 years, the Metropolitan Police admit they supplied information to the construction workers blacklist.
It's nearly two years since level 2 BIM was made a minimum requirement on certain public projects. But what actually is it?
Renowned water expert Prof. Martin van Veelen challenges political leaders to do more on safe and clean water supplies.
Inquiry criticises PwC for "milking the Carillion cow dry".
A recent roundtable discussed the future of transport in the UK – including the role of connected and autonomous vehicles.
Architects report cancelled projects and uncertainty concerns in a new RIBA survey on Brexit.
Quality helps eliminate defects, but it can also drive improvement and increase profit.
PII provides insurance cover against negligence claims and is widely used where services are being provided.
Rogers Stirk Harbour + Partners release first images of their planned new addition to the Toronto skyline.