- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 18 Jul 2017
Safe ductwork - Loss Prevention Standard (LPS 2084)
The Regulatory Reform (Fire Safety) Order 2005 requires that a building’s owner or workplace manager nominates a responsible person to identify all possible sources of fire and eliminate, or at least minimise the risk, to the building’s occupants.
Regular kitchen extraction cleaning will remove one of the most common causes of fire within the kitchen and is imperative to ensure the safety of the building and its occupants and reduce the risk of a fire caused by grease build-up in the extraction system.
Regardless of the efficiency of canopy filters, it is inevitable that grease deposits will build up over time in kitchen extraction ductwork and canopies. If left, grease will become baked on and carbonised making it extremely difficult to remove, thus reducing the effectiveness of the extraction system, potentially shortening the life of the fan and creating a serious fire hazard that may propagate around the building.
The Loss Prevention Standard (LPS 2084), published in May 2017 by BRE Global, seeks to minimise fire risk from ducting. It was prepared in response to issues caused by ineffective cleaning and maintenance and defines the Loss Prevention Certification Board (LPCB) requirements for the approval of companies carrying out inspection, cleaning and maintenance of ductwork systems that may be contaminated with combustible deposits.
Certified companies with LPS 2084 have to:
- Meet the requirements of the client contract.
- Document and report correctly.
- Identify and record areas of limited access where inspection, cleaning and maintenance are impractical and communicate these limitations to the client.
- Provide recommendations for access improvements to better facilitate the ongoing cleaning and maintenance of the ductwork system.
LPS 2084 is of great importance in an industry with little regulation.
Certified companies will be audited by BRE Global on a regular basis to ensure they continue to adhere to the requirements of the standard. Auditors will check records and supporting documentation covering the contract itself, storage and handling of cleaning materials, disposal, training and so on.
Specifying LPCB approved products and services enables the responsible person to reduce risk by showing due-diligence in the selection of products and services that can be trusted to perform as specified.
This article was originally published here on 17 July 2017 by BRE Group.
 Related articles on Designing Buildings Wiki
Featured articles and news
As the latest summer blockbuster 'Skyscraper' is released, we look at some of the best uses of buildings in film.
Read our introductory article on how to layout a building.
New cross-party report calls for combustible cladding ban to be extended to all high-rise residential buildings.
Dr Nicholas Falk, director of the URBED Trust, explains why metro cities are the future of urbanisation.
From next week, UK firms can bid for a share of a £12.5m fund to boost productivity, performance and quality.
A right to light generally refers to the right to receive sufficient light through an opening.
Interference and compatibility - the effects of electromagnetic fields in the workplace.
Important action is being taken to inspire young people to train as engineers.
A survey of Leicester’s historic buildings resulted in local listing being taken more seriously.
Demolition is the most high risk activity in the construction sector. Read our introductory article here.