- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 25 Mar 2018
Ronan Point was a 22-storey tower block in Newham, East London which suffered a partial collapse on 16 May 1968, only two months after opening.
A gas explosion resulted in the progressive collapse of an entire corner of the tower block, which killed 4 people and injured 17 other residents. The cause of the explosion was a resident striking a match to boil water which ignited the gas that was leaking from a joint in a newly-installed cooker.
The explosion blew out the load-bearing flank walls, which had been supporting the four flats directly above, lifting the ceiling and floor slab. This resulted in a house-of-cards progressive collapse as the floors above were then unsupported.
Despite the relatively low casualty rate, the impact of Ronan Point was dramatic. As the blame being placed on poor design and construction, public confidence in tower blocks fell dramatically, and this spelt the end of the high-rise and prefabrication as solutions to the post-war housing crisis.
The architectural profession was also badly tarnished by the event, and modernism in general, being synonymous with high-rises, suffered similar criticism. In the 20 years following the disaster, a large number of similar tower blocks were demolished and major changes were made to the building regulations.
At more than 200 ft tall, and containing 110 flats, Ronan Point was built by Taylor Woodrow Anglian using a construction technique known as Large Panel System building (LPS). This involved the off-site prefabrication of large concrete sections that were than lifted into position by crane and bolting together.
These sort of system-built blocks had been constructed en masse in the post-war push for increased housing provision. The previous year (1967), had seen the largest ever number of new flats and houses built – 470,000.
The inquiry into the disaster found that although the design had complied with the building regulations, there were several major concerns about the safety and stability of the tower which was not adequate for even small explosions or for expected wind loadings; nor would it be adequate in a fire, which could have lead to the structure bowing and subsequent collapse.
After the inquiry, the tower was partly rebuilt using strengthened joints which were designed to deal with these issues.
 Subsequent investigations
In the years following the inquiry, several people campaigned on the basis that it had unsatisfactorily investigated every issue.
Subsequent investigations, which led to the building’s eventual demolition, found that the revised wind loading assumptions were inadequate because they were based on the assumption that all the windows were closed. If, under heavy wind loading, a window was broken or was left open, pressure on one side of a wall panel and suction on the other could have led to a similar failure.
Other construction defects were found, such as the fact that, instead of being spread evenly along the panel, the whole weight of each wall panel was being supported by the panel beneath by two steel rods, resulting in very high stresses. Also, strengthening brackets fitted during the rebuilding were often incorrectly attached, having been fastened to the thin concrete surrounding the hollow-core slabs.
Cracking in the load-bearing concrete walls was deemed to make the building unsafe for habitation, and the council decided to demolished it in 1986. The Great Storm of 1987 saw hurricane-force winds that might have caused the building to collapse.
 Changes to Building Regulations
In the wake of the Ronan Point collapse, changes were made to the building regulations. ‘Disproportionate collapse’ is now covered in Part A, and requires that ‘the building shall be constructed so that in the event of an accident, the building will not suffer collapse to an extent disproportionate to the cause.’
Measures were also introduced to safeguard buildings in the event of an explosion. These stipulated that all new buildings constructed after November 1968 and taller than 5 storeys, must be capable of resisting an explosive force of 34 kPa (4.9 psi). Existing buildings could be resistant to the lower force of 17 kPa (2.5 psi) if the gas supply was removed and flats were retrofitted with electric cooking and heating.
 Related articles on Designing Buildings Wiki
- Adam Curtis - The Great British Housing Disaster.
- Approved Document A.
- British post-war mass housing.
- De la Concorde overpass collapse.
- Defects in construction.
- Grenfell Tower fire.
- Modular buildings.
- Offsite manufacturing.
- Structural failures.
- The structural condition of Easiform cavity-walled dwellings (BR 130).
Featured articles and news
Dr Nicholas Falk, director of the URBED Trust, explains why metro cities are the future of urbanisation.
From next week, UK firms can bid for a share of a £12.5m fund to boost productivity, performance and quality.
A right to light generally refers to the right to receive sufficient light through an opening.
Interference and compatibility - the effects of electromagnetic fields in the workplace.
Important action is being taken to inspire young people to train as engineers.
A survey of Leicester’s historic buildings resulted in local listing being taken more seriously.
Demolition is the most high risk activity in the construction sector. Read our introductory article here.
BSRIA report on the domestic boiler market, with China recording the most 'dynamic market uptake'.
Do we really know everything important about the impacts of our infrastructure projects? And if we don’t, does it matter?
Former Chief executive Richard Howson blames government for being 'poor payers'.